Hey see performance tuneup times one system. Inspect blower, evaporator and ductwork. Check temperature difference in amp draw. Checked thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacture specs at this time.
Installed ECM blower motor, checked everything is working properly.
Completed diagnostic, ecm blower motor is bad. Customer will call us tomorrow, because he may have another company coming out. Also need to call with a price. M#FEM4P3600AT1. S# A122469592
Heating performance tune up times one system. It was suspect blower, evaporator and ductwork. Tightened all wire connections. Tested heat rise .System is a heat pump. Heat rise is 40Â°. Test amp draw on heat strips. 21 amps. Check outdoor unit. Refrigerant level good at this time. Tested defrost cycle. Coil is clean test the thermostat for proper operation. System operating at manufacturer specs at this time.