He was awesome. He knew exactly what needed to be done, and went above and beyond to take care of me. Thank you AC Pros and Joel!
Joel always does a great job. Very informative!
I have used AC Pros for 17 years. They are honest, great and reliable. Absolutely recommend!!!
Great Service - Jeff was “Very Professional and pleasant - Thank you
Joel has been our AC Pros service technician for several years. He is always, polite, informative, thorough, and a really likable guy!
Perform 1 system heat Maintenance changed customer supplied filter tested all safety components checked for co found none checked the heat exchanger looks good recommended rheme halo system is heating properly at this moment
No cool. Found condenser not running. Run capacitor had loose terminal and a burnt end. Removed and installed new turbo. Unit is a 2000 model. It had the factory hard start kit on it which was defective. Removed and installed 321 hard start kit. Wash condenser coil. Added less than 1 pound of R 22. Documented data plates and sent to Russ.
Maintenance check is complete, refrigerant were in range, compressor amps, blower motors and run capacitor at compressor is getting to a place were we need to replace it, declined repairs at this time. Talked to homeowner about Reme Halo and ductwork cleaning, will think about it. All four systems is in good working condition.
System was low on refrigerant, also performed electronic leak search. Evaporator coil is leaking, system is carrier system is 6years old, not sure about warranty. M#FX4DNFO43L00ACAA S#3815A85517. Celeste can you check warranty and get with homeowner on price, thanks.
Condenser fan was not working, installed 45/5microfared turbo run capacitor. Checked refrigerant levels, ok.
Completed diagnosis on upstairs system, refrigerant levels and sub cooling is in range. Also checked the square footage, system is sized correctly, 22 degree temperature split. Possible problem, room is over garage and floor is creating heat. Need more insulation under gararge floor
Checked refrigerant for all three units, Masterbedroom system appears to be low on 410a, its a new construction home, so shoes still under a 2 yr. Labor warranty. Advised to invest in Rene Halo uv lights. Also has Erv fresh air purifier. There are no uv lights present at the time.
Post install walk-through on recently installed equipment and maintenance on older system. Inspect blowers, evaporators and ductwork. Treated drain lines with drain solutions. Test thermostats for proper operations. Newer system is hung square and level. Drains are flowing properly and PVC is insulated.Check outdoor units. Proper breaker and disconnect is installed in the new system. Refrigerant levels good on both systems. Run capacitor and contactor OK on older system. System is operating at manufacture specs at this time.
Arrived to unit extremely low on refrigerant added 3 lb if 410A to get customer cooling for the night we will conduct a leak search tomorrow and go from there
Perform leak search found leak in evaporator coil and condenser arrived to low again on refrigerant almost dead empty will have Russ come out tomorrow and give customer options customer has 2 systems
Completed maintenance inspection, systems are about a year old, all the units in manufacturers specifications. No problems found at this time. Also washed condenser coils.
Perform 2 systme maintenance checked pressures split both systems were slightly low on refrigerant added 1lb to each to reach design subcool under labor warranty advised customer to replace both filters asAp and recommended duct cleaning both systems cooling properly at this moment
Condenser coils are clean, replaced media filters, drains lines are clear. Compressor amps and all other electrical components are in good shape and up to specifications.
Indoor/outdoor systems were not communicating on upstairs. Replaced 40 microfared Turbo run capacitor. Everything is working. Declined. Gold membership at this time.
Perform 1 system maintenance checked pressures split and amp draws specs are on maintenance form system is currently cooling properly at this moment