Service Tech Joel is always helpful & knows what he is doing!
Professional, COVID safety compliance was adhere to, transparent as to the issues. Thank you
Cole is dependable & all the things I said in above question.
We always trust AC Pros! Been their customer for more years than we can remember!
Always the best service when the professional educates me on how to get the best performance from my system. Jason not only knows the products and the physics but does an excellent job of explaining them.
Arrived to no cool on downstairs diagnosed weak capacitor replaced it with turbo downstaora is cooling properly . Upstairs stopped working when I arrived diagnosed compressor winnings weak 20 year old system will have Russ come out and Bruce options
Perform 1 system maintenance checked split and pressures changed out filter customer supplied washed condenser coil system is cooling properly at this moment
Completed diagnosis, ductwork is in valted ceiling, no adjustments can be made.
Removed dirty 1 inche filter that sucked up inside airhandler, causing system to freeze up. Also run capacitor was way out range. Installed Turbo 45/5 run cap, checked charge 12 degree sub cool. Everything is working good.
Customer refused service, told me to get out of his house.
Completed diagnostic, evaporator coil is frozen, can we reschedule for tomorrow, She has one system.
Completed maintenance check, cleared drains, blower motor, compressor amps, fan motor and change out media filter. Freon levels were low, declined repairs at this time.
No cool single system. I was here earlier in the week and installed new blower motor. Outdoor unit not coming on. Broken wire was the main issue. Other issue is this system is a two-step two-stage outdoor unit. It was not wired correctly for two-stage. First page is all that has been controlling this unit since it has been installed in 2017. I made adjustments to make the unit come on. Advise client to call Monday and get on the schedule toGet on the schedule for the maintenance. System is cooling at this time.
Return today to install new one horsepower variable speed blower motor. System operating properly at this time.
No cool single system. Found blower motor not operating. Removed module and put on temporary. System is cooling at this time. Cost of the motor is $1749. New furnace is 5500 Office can order tomorrow morning and schedule date for me to return to install motor.
Downstairs system was low on R22, customer declined replacement of system. Charged with 2 pounds of R22, no guarantee or warranty on refrigerant.
Completed diagnosis, found primary drain pan broken at the fitting. Leaking into emergency drain pan. Evaporator coil needs to be replaced. Per Russ Teager quoted price 3,350.00. Customer will call us she will put 1,675.00 down before we order the coil. M#ASL3614A22E. S#10F06824SBfb
Perform 1 system maintenance changed filter washed condenser coil also fix pvc leaking from pvc fitting when we installed the coil last summer added 1 lb of refrigerant to get subcooling to 8 recommended to add surge protectors to system. system is currently working on manufacturers specs
Arrived upon unit frozen up changed filter with customer supplied filter and added 1 lb of r22. System is showing age effects I inform Mr Castillo Iâ€™m not sure if the system will last him all summer. will have Jim contact him to give him a system replacement quote can confirm system is cooling at this moment.
Single system no cool. Found primary drain clogged up tripping the float switch. Installed quick blast and clear drain. System is operating at manufacturer specs at this time.