Checked flame sensors and ignighters, replaced filters and performed co test as well as inspected flu pipe and blower motors
Making texas happier, one customer at a time.
Performed maintenance on 2 systems, no cracks detected or gas leaks found. Heat pump reversing valve, refrigerant levels, run capacitors are good. Everything is operating properly. Also renewed Gold membership for 2 systems.
Perform 2 systme maintenance checked pressures and split heat pump systme checked out good. Gas furnace system is a low on refrigerant conducted a electronic leak search found leak in evaporator coil system is still on warranty with Trane pics of model # and serial number of coil in service titan
Left side system Inducer fan motor- .18 Inducer fan motor capacitor- 3.9 Blower motor amps-1.98 Blower motor capacitor-NA Air proving switches- ok High temp limit switch- Ok Gas valve- operational CO LEVELS- Ok Filter- Changed Igniter ohms- 49 Ductwork- looks good Flame sensor- Ok Flame looks good Tighten all electrical connections Control board- Ok Thermostat- Ok Recommend a surge protection and ATTIC EVALUATION. Right side system Electric heat strips- 19.7 Blower motor-2.01 Contactor-Ok Tightened all electrical connections Controls- Adjusted airflow on each system due to loud registers and velocity of. Fm from the vents.