Completed tune up form and reviewed and emailed to customer. System is brand new and so is insulation and duct work .
Upstairs system had carbon monoxide leak 5ppm recommended replacing the furnace
I was Dispatched to a call for poor airflow in some rooms and too much in others. I found one of the Bedroom's had a closed vent. I opened the vent and the room began to cool. I inspected the Ductwork. There are no Dampers to adjust. I did what I could with the Ductwork but she wants a price to repair/replace.
No display at thermostat because drain line was clogged, causing float safety to Tripp. Cleared out drain.
AC performance tuneup times one system. Changed out filter and cleared and treated primary drain line. Inspect blower, evaporator and ductwork. Check thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. Washed condenser coil. System operating at manufacture specs at this time.
Thermostat was faulty, need to order Trane XL50 communicating. Thermostat.
Completed diagnostic, possibly control board is faulty, not bringing on condenser. Need Tech support from Trane.
Installed Trane 850 comfort link thermostat, also replaced 25 microfared run capacitor at compressor. Reprogrammed thermostat everything is functioning properly.
Perform 2 system AC maintenance checked refrigerant levels tested capacitors and contactors. Checked amps on condenser. Washed condensers both systems cooling properly at this moment
Post install walk-through on recently installed equipment. Verified that all is good with the heater section of the new unit. Could not check charge today because it is not above 60Â°. Office will call and schedule a date to come back and check the charge on the air conditioner. Also did air balance to achieve more airflow to the master bedroom and living room. I will check on the status whenever I come back to check charge.
Heat performance tuneup times one system. 25Ã—36Ã—1 filter is almost needing to be changed. Client did not have any at this time. First time here to do a heat maintenance. Do you to the lack of area space the filter has the inside of the burner box is very very worn. No carbon monoxide or gas leaks were detected. System is almost 17 years old. Tightened all wire connections. Cleaned flame sensor and induce report. Furnace cabinet had many air leaks due to the poor construction install. Recommendation today is to replace the system given the current state of it.
Arrived to water on pan clean p trap and added p trap to secondary drain to stop it from getting on pan
Check all operations on system, everything was functioning properly. No noise was found when operating in heat mode. Run capacitor at condenser was weak and potentially failing, added Turbo capacitor and also purchased a Gold membership for 1 system. We will schedule fall for 1st check.
Arrived to find blower not running and after running a blower test found it to be bad which can be confirmed by manually trying to spin the wheel. Quote will be given for repair and comfort advisor will be set up in the morning to give options on replacement. Customer said they have some airflow issues as well. Can confirm heat is not running at this time but I informed them they can have portable heaters if need be.
Thermostat blank. Mad necessary repairs to low voltage. 5 amp fuse wires were heavily corroded. Original fuse defective. Installed new 5 amp fuse and remounted thermostat to wall. System is 13 years old. Ducts are VERY dirty. System is working at this time.