As good a service I’ve ever had from you.
We love seeing Joel for our twice a year inspection. He’s so knowledgeable about our system that we know he won’t ‘steer us wrong!’
I will always ask for Joel Sisk!
Heat maintenance on single system, checked for gas and carbon monoxide leaks no detection. Temperature rise is 35, inducer draft motor, flame patterns and limit switches are working properly. Recommended adding surge protectors declined all repairs,. Price total $348.50
Arrived to find water on emergency drain pan blew drain outs and treated it advised maintenance on drain lines they were really dirty clean water off pan system draining properly
Arrived to find bad capacitor warranty out didnâ€™t have the same size in my truck installed a turbo system cooling properly at this moment
Primary drain was clogged and tripping the in-line float switch. Supported drain line better to give it better fall to the drain hub. Decided not to charge customer since we did his maintenance a week ago
Heat performance tuneup x 1 system. Change out filter client supplied. Check all safety features, high limits and rollouts. System operating at mfg specs
perform 3 system heat maintenance checked safety components clean coils on mini split cleaned both had flame sensors and co levels all 3 systems heating properly at this moment
Heat maintenance inspection: Recommended adding Reme Halo to system to clean environment within home, such mold, dust, bacteria, gases and odors. Also Attic insulation needs to be added, Homeowner will consider having problems addressed. Also no gas or carbon monoxide detected, flame pattern, hot surface igniter was in good shape. No other problems found. Price on Reme Halo $995.00 includes installation.
Heat performance tuneup times one system. Client had already changed his filter. Inspect blower, evaporator and ductwork. Checked all safety features hard limits and rollouts. Check heat exchangers for cracks, found none. Clean flame sensor, and do support and ribbon burners. No carbon monoxide or gas leaks detected. Test thermostat for proper operations. System heating at manufacture specs at this time.
Heating maintenance times one system. Change out filter client supplied. Check all safety features high limits and roll outs. Inspect blower, evaporator and ductwork. No gas leaks or carbon monoxide detector then home. Checked heat exchanger for cracks found none. Test thermostat for proper operations. System operating at manufacture specs at this time.
Heat maintenance, everything is properly, no problems found. Celeste forgot to clock out. Got side tracked. Out at 4:30.
Completed maintenance for 3 systems, all filters needs to be Changed they are really dirty. Upstairs electric heaters are working good. Downstairs/ Masterbedroom flame patterns,flame sensors, no gas or carbon monoxide leaks detected. Recommend installing Reme Halo to upstairs Masterbedroom system for $995.00 installed. Also homeowner will renew membership in spring time we just need to call her.
Heating performance tuneup times one system. Cleaned flame sensor and into support. Blew out burner and ribbons. Inspect blower, evaporator and ductwork. Ductwork needs to be cleaned. Check for carbon monoxide found none. No gas leaks detected in home. Checked thermostat for proper operations. System operating at manufacture specs at this time.
Primary drain pan is cracked leaking water into secondary drain pan. Quote per Russ Teager $3,575.00 10yr. part 2 yr. Labor. 2 ton horizontal Trane box evaporator coil, supply plenum, secondary drain pan. Also 4ft of 8 and 6 flex duct, Masterbedroom system. Homeowner will give us a call when ready.
Heat maintenance: return filter was dirty causing error code. Flame pattern, and sensor is in good working order. No gas or carnon monoxide leaks. System is in good working condition.
Heater inspection, flame sensor/ flame pattern/no gas or carbon monoxide leaks, attic insulation is in good Shape as well as filter. Furnace is in good working order.