The best tech that’s every been to our house.
Very timely and knowledgeable.
Jeff came when promised, completed the repair quickly. Thankfully cool again
Jeff repaired our A/C when he stopped working. He was very knowlegeable, friendly and efficient. As a customer for over 15 years, AC Pros has never let us down! Thank you!!
Technician was extremely polite and caring about the issue on a late Sunday night. He fixed it fast and I was very satisfied with his work. But... After one hour the same problem came back again and we had no air for sleeping.
Most conscientious ac tech we ever had
No cool single system. Upon arrival found outdoor unit not running. No power at the contactor. Advise client to check breakers inside the home. He did and reset and system came on. System is a 30-year-old Goodman condenser coil is very bent up. Possibly causing the condenser to have too much pressure which caused the breaker to trip. Not 100% sure but system is cooling properly at this time.
Completed maintenance check out, both compressor are running hi amps on start up. Washed condenser coils, flushed drains, system are noisy because of universal fan motors. Recommended replacing systems.
Completed diagnostic, wires are burnt and start kit is shorted out on upstairs system. We need to set up comfort specialists to give him a call asap about a new system.
Upstairs system is partially frozen, added 2 pounds of R22. Customer is having someone out to quote on new system.
Arrived to both systems down diagnosed bad condenser fan motor on smaller system, system is 19 years old Russ will come out tomorrow to give Brian options on system replacement. Main unit has a bad blower motor and module jumped module to get blower up and running for right now will contact them with info to replace blower motor and module
Installed EEV valve and expansion head, checked all operations working fine. Customer refused to pay the balance.
Maintenance check is done, washed condenser coils, flushed drains. Run capacitor/compressor amps are good. Replaced media filter, Temperature split was good.
Completed diagnosis, blower module is bad for master bedroom furnace. Need to order part and schedule call. M#TUD060R9V3J1 S#R293PKH1G. Customer will put 33% down. Balance $368.83
Installed 410a expansion valve and filter drier, charged system with 10 pounds of 410A. Everything is working fine.
No cool single system. Arrive to find indoor unit running and outdoor unit night went outside and found run capacitor swollen. Removed and replace with new turbo 200 X had to cool down condenser fan motor due to excessive heat once unit was started Iâ€™ll let pressures run for 15 minutes and added3 pounds our 410 a. System is cooling properly at this time.
Arrived to no cool diagnosed bad condenser fan motor and module will get in contact with office with info
Perform 1 system maintence checked pressures and split changed filter and washed condenser coil specs are on maintenance form system is currently cooling properly
System was low on refrigerant(upstairs) 410a. Performed electronic leak search, evaporator coil is leaking refrigerant. Customer want to proceed with replacing evaporator coil. We need to call and schedule installation. Also give quote. M#4TXCB036BC3HCBA S#11303N695G
Arrived to condenser off switched float switch head rewired to furnace instead of condenser no charge due to we were just out here for maintenance system cooling properly at this moment
Completed diagnostic, expansion valve is restricted in airhandler. Systems is R22 8 to 10 pounds. Need to order part, one system. M#4TEC3F60B1000AA. S#11302R7S1V