Jeff was prompt in calling and coming. No wasted time or effort. Curious to check on all performance items and then report all findings. A routine seasonal maintenance check performed well. He paused to take performance and air filter questions. Very knowledgeable. Trusted too Nicely done. Thank you
Jeff quickly solved my problem
On time and efficient
He showed up on time and got my air running again quickly, I asked him other info about my vents and other things and he answered all my questions. I will definitely be using them again 😁
Great job. Feel safe.
Francisco went above and beyond to make sure we got the correct part to fix our AC.
Fransisco was great. He found the problem quickly and explained it in a very accessible way. An overall great experience.
Perform 1 system heat maintenance checked safety components checked heat exchanger and co levels cleaned flame sensor system is heating properly at this moment recommended duct cleaning due to old ductwork
Heating performance tuneup times one system. Advised client that the filter needs to be changed within the next two weeks. Check all safety features high limits and roll outs. Engaged test mode on the IFC three times. Tested temperature rise 42Â°. Check blower, evaporator and ductwork. No Carbon monoxide or gas leaks detected in home. Remounted thermostat with a blank off plate behind it. System operating at manufacture specs at this time.
Performed maintenance check on heater, everything checked out no problems found at this time.
Completed heat check, found bare places so attic insulation needs to added, to control temperature. Also not enough ventilation on roof. Flame patterns, igniter and flame sensor are in good shape. No gas or carbon monoxide leaks and temperature rise and gas pressure is good. Changed out media filter. Homeowner purchased a Gold membership.
Primary drain was clogged up on the drain line causing the system to shut off. I had to re-pipe 4 feet of the PVC because the copper was no good. System draining properly and operating properly at this time
Removed extremely dirty filters clean grills and added 1 lb of 410 system cooling properly at this moment
Heat maintenance check: flame is sensing low micro amps, needs to be replaced. Also recommended adding Reme halo, declined repairs right now. Attic insulation is ok, return filter is dirty homeowner will replace it. Carrier furnace M#310AAVO36070AAJA. S#3804A27330. price on Reme halo$995.00.
Arrived to find system frozen will let it drout out and come back to diagnosed
Heating performance tuneup times one system. Changed out filter client supplied. Inspect blower, evaporator and ductwork. Tested all safety features higher limits and roll outs. Clean flame sensor, Induce her port and ribbon burners. Check thermostat for proper operations. No carbon monoxide or gas leaks detected. Hit exchanger still look like new no cracks. System operating at manufacture specs at this time.
System was drout out found system low on refrigerant r22 found leak in evaporator coil system is fan coil had Russ come out and give options
Arrived to find system frozen turn system off we have to let system drout out and come back tomorrow
Heat maintenance one system, cecked for gas and carbon monoxide leaks gas pressure, temperature rise and inducer draft motor was functioning properly. Recommended surge protectors.
Completed diagnosis, no problems found at this time, flame sensor micro amps were at 2.5 Which was good.
Perform 2 system heating maintenance on recently installed systems tighten connections changed customer supplied filter tested safety components and co levels found no issues system is heating properly at this moment recommended rheme halo and attic Insulation top off
Perform 1 system heat maintenance checked safety components changed customer supplied filter checked co levels recommend attic insulation system is heating properly at this moment