Francisco was polite, efficient, thorough and problem solving.
The technician was knowledgeable, respectful and efficient.
Working with AC Pros has been awesome, everybody is helpful and nice.
Jeff is awesome!
Joel is great and very responsive
Set zone dampers where each zone will open and shut accordingly. System is operating properly at this time. # no
System not keeping up. Check charge and found system to be at least 2 pounds low on our 22. Gloria stated she would like to see what her home warranty will pay for.
Arrived to t stat off found wire loosed tighten connection system cooling properly
No duct fans in attic will consult Russ on what needs to be done and contact nikki on price qoute
John and I walked around to see which vents were blowing and which were not blowing. Three vans downstairs never blow. System is keeping 72Â° inside the home downstairs. 75 upstairs.
Perform 2 system maintence checked pressure and split upstairs system was low on refrigerant indicating a leak sandy wanted to bandaid so I added 2 lb system both systems cooling at this moment
Lisa stated that the upstairs unit was malfunctioning. Check the filter and it was OK needs to be changed though check thermostat. Put system into second stage and check charge. Refrigerant level is good at this time. Found condenser coil completely clogged with Cottonwood. Cleaned off coil and unit next to it. System is cooling properly at this time.
Connected and secured primary drain line on inside and outside of house, For upstairs.
Perform 1 system maintenance change filter customer supplied washed condenser coil checked split and pressures drains are not sloping correctly and need to be reran they run over 50ft and advised Mary to have a plumber and reran drains from bathroom sink up to the attic and have us come out and tied into condensating line that way she donâ€™t have problems in the future can confirm system is cooling at this moment
No cool single system. Client stated that it didnâ€™t seem like it was keeping up. Went to outdoor unit and found common wire burnt on the run capacitor. 55+5 run capacitor was basically dead. Removed and replace with turbo. Part comes with five year warranty. Check charge and refrigerant level is good at this time. System cooling properly at this time.
Arrived to no cool dignosed compressor not running installed turbo condenser is from 1994 showing signs of age and compressor amping high customer wants a qoute on replacing condenser will have Comfort consultant come out and give him options tomorrow can confirm system is cooling
Arrived to compressor not coming on dignosed a bad capacitor replaced with turbo system cooling properly now customer had senior citizen/military 10% off coupon
Arrived to clogged lines cleared installed quick last and blew with nitrogen advised Adam to get a plumber to go under house to rehang the drains from the outside it looks like drains backpitching he said he would do it himself drains clear at this moment
Replaced condenser fan motor for #1 system, 22volt 825 rpm. Checked charge everything is working fine.
Downstairs system was on R22, charged with 5 pounds. No warranty or guarantee on refrigerant.