Told us our new unit you installed is still running fine !! Joel was pleasant and informative !!
Arrived to leak search found leak on condenser coil mr Simonds talked to Russ waived leak search per Russ
Customer decided to cancell service over the phone but wants maintence on system done will talk to office Monday to schedule
Perform 2 system maintenance upstairs system was low on refrigerant gave Vicky several options including a leak search she decided to go with the bandaids and added 4 lb for the moment talked to Vicky will have Jim contacts her to give her a quote on new system. Drain lines are a concern talked to Tera and also told her about recommending a solar fan the attic is too hot and theirs nothing to release some of that heat. Washed both condenser coils they were really dirty. Can confirm both systems are cooling at this moment.
No cool downstairs. Nest Thermostat was indicating it could not operate the equipment install. I found a short on the contactor outside. Removed and replaced with new 1.5 pole contactor. System came on and operating properly at this time. New thermostat was not needed. Advise clients that our office check the warranty status of the equipment and it is only good for 5 years. Contractor did not register equipment within 90 days. System is operating properly at this time.
One system maintenance on a train unit. Condenser and furnace were both checked, coil was checked. Iâ€™ll capacitors hard start kit pressures and air temperature checked and shown to customer. Recommendations are to fix the drain lines with proper pitch and add paraphrase.
No cool. Found run cap weak. Replaced with Turbo 200. System came on and operating properly at this time.
AC performance tune up times two systems. Inspect blowers, evaporators and ductwork. Test thermostats for proper operations. Treat drain lines with white vinegar. Check outdoor units. Refrigerant levels good at this time. Test capacitors and contactors. Wash condenser coils. Systems operating at manufacturer specs at this time. Disconnect went bad after I turn them on after cleaning them I advised Alan that I bypassed it and that we would address it next year. Leaving quotes for 4 inch filter racks one for upstairs one for downstairs. Systems have always had a 1-inch filter rack. The downstairs is 20 x 25 x 4 and the upstairs is 14 * 25 * 1. Cost per filter rack is $299
Checkup done on trane unit. All system components are within range.
Hitting performance tune up times one system. Filter had been changed recently by client. Inspect blower, evaporator and ductwork. Test all safety features Heating performance tune up times one system. Filter had been changed recently by client. Inspect blower, evaporator and ductwork. Test all safety features high limits and rollouts. Tightened all wire connections. Tested thermostat for proper operation. System operating at manufacturer specs at this time.
Heating, stirring up times one system. Change out filter client supplied. Inspect blower, evaporator and ductwork. Test all safety features High limits and roll out. Test thermostat for proper operation. I know our connection. System operating at manufacturer specs at this time.
Replaced leaking Goodman coil with new Trane box coil - 10 year parts & 2 year labor warranty
Arrived to find system empty of freon and not coming on outside. Hard start kit was also blown indicating system was running with very low freon for some time. Need to set up a time to come out for an estimate.
Arrived to find gas valve turned off. Turned back in and heat is running at this time
Both systems functioning properly in heat mode at this time.
Providing an estimate on unit replacement in Richardson