Francisco did a outstanding good.Great tech.Thank you
Told us our new unit you installed is still running fine !! Joel was pleasant and informative !!
Calibrated thermostats in the primary residence. Still have no answers on the mini splits and air handlerâ€˜s. I advised Everett that I would have answers before next Friday.
Checked refrigerant levels, cassette that on East side is about 3 degrees cooler than West side cassette. Misty homeowner said that youwill look into trying to find WiFi thermostats.
Replaced indoor blower and module system cooling properly at this moment
Arrived to no cool indoor blower and module bad temporarily fix with one of our used motors and modules to get customer running for right now. We will need to replace variable speed blower and module
System was low on refrigerant, customer declined leak search or adding any refrigerant.
Post install walk-through on recently installed equipment. Also checked out mini split to find out why one side is blowing colder than the other side. Adjusted charge on XV outdoor unit to cheer a 10Â° sub cool. Drains are slow properly units are level and square.I will contact train in the morning and give them the scenario that is at this location to find out how we can rectify the problem.
AC performance tuneup times one system. Inspect blower, evaporator and ductwork. Check thermostat for proper operations. Taped up air leak at the blower door. Check outdoor unit. Refrigerant level good at this time. Wash condenser coil. Drains flowing properly at this time. System operating at manufacturers folks at this time.
Cleared drains, checked blower/fan and blower amps, which was in range. Return filter and electrical components are ok. Condenser coils are clean.
REPLACED COMPLETE SYSTEM - 10 YR TRANE PARTS WARRANTY - 5 YR DEALER LABOR WARRANTY - 5TH YR MAINTENANCE ON NEW EQUIPMENT ***installing temp xr16 c/u until xv18 arrives***
Arrived to compressor not coming on due to dead capacitor replaced with turbo system cooling at this moment
No cool single system. Found condenser and fan not running and overheated. Turned off power check the run capacitor and found it to be dead. Install new turbo 200 run capacitor which comes with a five year warranty. Refrigerant charge an amp draw seem to be good since unit is cool down. System cooling properly at this time.
Arrived to leak search found leak on condenser coil mr Simonds talked to Russ waived leak search per Russ
Customer decided to cancell service over the phone but wants maintence on system done will talk to office Monday to schedule
Perform 2 system maintenance upstairs system was low on refrigerant gave Vicky several options including a leak search she decided to go with the bandaids and added 4 lb for the moment talked to Vicky will have Jim contacts her to give her a quote on new system. Drain lines are a concern talked to Tera and also told her about recommending a solar fan the attic is too hot and theirs nothing to release some of that heat. Washed both condenser coils they were really dirty. Can confirm both systems are cooling at this moment.
No cool downstairs. Nest Thermostat was indicating it could not operate the equipment install. I found a short on the contactor outside. Removed and replaced with new 1.5 pole contactor. System came on and operating properly at this time. New thermostat was not needed. Advise clients that our office check the warranty status of the equipment and it is only good for 5 years. Contractor did not register equipment within 90 days. System is operating properly at this time.