Customers gonna hold off the heat strips Because going to talk to wife about new system due to the price increases that are going to be happening.
Apon arrival checked in with customer the following are my findings Found the Heat pump side of the unit operating however the emergency backup was not on will be contacting customer tomorrow with time and availability for part please see pictures attached
Heat Pump Repair - Customer has a heat pump and the plug on condenser board was slightly pulled out which prevented 24v from pulling contactor in . System is heating properly .
Performed maintenance on 3 systems (heatpumps)
I was Dispatched to perform a One-Time Maintenance and to remove a Bulb from the Return. The Bulb is a Horn for an Alarm System. It is situated in the Return so the Horn will travel throughout the House through the Ductwork. I cleaned and serviced the System and checked System Operation. Everything appears to be functioning as expected. At this time. The Customer states he would settle up with the Office.
CFM defective. Removed and installed New universal. Russ to give quote tomorrow for new system.
Compressor not coming on. Repaired chewed high voltage wires going to compressor and fan motor. Also replaced contractors, which was grounded out. Check amps and charge, everything is working great.