Good service and Michael explained what he planned on doing doing the entire service call.
All business and sharp!
Howard was excellent
Our technician was very helpful and knowledgeable. Thanks for a good experience.
Michael was knowledgeable courteous efficient tech Perfect job performance fantastic fantastic ,and again fantastic ,
Mike came in morning 11.30 Am and was very meticulously performed the tests calmly and fixed the issues. Appreciate his awesome service, I am very happy with his service,
The two guys explained the problem very well.
Howard is a great technician and a delightful human being. Ashley calls me to set an appointment, she lets me know when they are on their way to my house, the technicians are professional and very respectful of my time and my home.
Diagnosed a broken condenser fan motor on a Nordyne AC.
Fixed a Trane heatpump that needed a new capacitor under warranty.
Fixed a Carrier furnace that had a broken ignitor.
Replaced a broken Nest thermostat to fix a heat pump AC in Rowlett.
Diagnosed a Carrier heatpump with a broken reversing valve.
Tuned up a Carrier heat pump for the fall.
Replaced a broken control board on another Goodman AC.
Fixed a Goodman furnace that had a broken gas valve and rollout switch.
Diagnosed a broken controller on a Goodman furnace.
Checked a built in wall heater, and made sure it worked good.
Diagnosed an Aire-flo AC that had a leaky air handler.
Fixed a Carrier heater that had bad wiring to its thermsotat.
Fixed a Carrier air handler that had insulation sucked through fan.
Fixed a broken Goodman heater that had a bad ignitor.
Fixed a Lennox unit that had a dirty sensor.