Matt was quick and had us back up and running in less than 30 minutes.
Polite courteous young man show me what could’ve been a future problem was able to clean my unit for me without having to come back Explained everything
Better than expected because I thought there was a major issue but it turned out to be minor.
Matt came in and addressed the problem. Fixed the AC. Very personable, good work ethic.
Fixed a Carrier AC that had damper motors broken and a damper sticking.
The primary line was clogged so I cleared it, and I vacuumed the excess water in the emergency drain pan to prevent any leak coming from the unit.
Replaced a 70uf + 5uf capacitor, and a 10uf run capacitor. Delta T is 20 degrees and the filter is clean.
Installed a new inducer motor in furnace, unit is heating again
Cleared primary and secondary lines and added a hanging kit to ensure proper drainage.
Replaced a disconnect and filter. The Delta T was in a good range and the run capacitors were good. There are no mechanical failures at this time.
Fall maintenance was performed. Everything is running fine and the system is ready for the winter!
Fixed a Trane furnace that needed a new inducer.
Diagnosed and fixed a Lennox furnace that needed maintenance.
Diagnosed a broken inducer motor in a Trane heater.
Fixed a Trane furnace that needed a few connections repaired.
Replaced the old condensing fan motor with a brand new 1075rpm motor and now the unit is cooling again!
Fixed a pair of York ACs that had clogged drainlines.
Fixed and replaced a bad capacitor in a Goodman AC.
Fixed a York furnace that had a dirty sensor.