Good service and Michael explained what he planned on doing doing the entire service call.
Ben is friendly, knowledgeable, and a man who seems to care about his customers. He has been here before and we would be happy to have him here every time we call for service. Since we have a contract with ACwizard, the call was covered because the repair turned out to be minor to fix and he was able to do the Spring Maintenance at the same time. That was a blessing! Thanks Ben!
We've used AC Wizard for several years at two different homes. Their technicians have always done a great job, whether it was a new system, regular maintenance, or problem repair.
Venny S did a great job with fixing the problem and educating me on various issues. I was very happy with his service and also with AC Wizard.
My fan motor on my heater went out. Chad figured out the problem quickly and didn't have the motor with him. Order the motor needed and picked it up and intstalled it 8 AM the next day. Excellent service. Did not rate the price because this work was done under American Home Sheild.
This technician was so professional from the door,he introduced himself,explained what he was doing and why. Handled himself in the proper way.
Yearly heater check up on maintenance contract so there was no charge!! Technician was superb, on time and very courteous.
Chad from AC Wizard arrived on time and quickly went to work doing our semi-annual service check. He was professional and polite. He even had "booties" on his shoes, so he didn't get the carpet dirty. We've done business with this company for several years, and their service representatives and the work they do are always top notch!
Antoine is very professional and efficient. Great job.
My technician was well mannered and went to work immediately taking care of his job. He explained his work when finished.
Fixed a Goodman AC that had broken hanging straps making it unlevel.
Fixed a York furnace that had a broken control board.
Diagnosed a Amana heatpump with a locked up compressor.
Fixed a Trane AC that had a leak.
Fixed a broken Goodman heater that had a bad ignitor.
Fixed a Lennox unit that had a dirty sensor.
Fixed a Carrier brand AC that had a broken control board.
Fixed another York that had a brooen capacitor.
Fixed a Lennox AC that had a clogged drain.
Fixed a Lennox AC that had a short in the thermostat wires.
Fixed a Carrier AC that had a clogged drainline.
Checked a Carrier AC and replaced a dirty filter.
Fixed a Lennox AC that had a shorted thermostat wire.
Fixed a Carrier AC that had a leak.
Diagnosed a Ruud AC with a broken evaporator.