Overall great experience. Thank you!
I felt safe being in the house with 2 technicians on my own. Guys got to the route of the problem and solved it. Even cleaned up after themselves. Would definitely use again!
No one wants to stay in their house with no heat. My heat went out on Sunday and I received a service call first thing on Monday with a service time. The technicians were courteous, professional and knowledgeable.
Our tech was great
Greg is the BEST!!!
Great job! Nice customer service, communication with quick and efficient repair.
Very happy with job performance
Best service AHS has ever sent to my home.Great, courtious guys. Thank you. Merry Christmas
Fixed a Goodman furnace that had a loose wire connection.
Fixed a Goodman furnace that needed a new blower motor.
Diagnosed a broken inducer assembly on a Trane furnace.
Fixed a Trane furnace that had a broken blower fan.
Replaced a bad run capacitor. Unit started right up, and is heating again!
Fixed a Trane heatpump that had a broken TXV.
Fixed a Lennox heatpump that needed a new TXV.
Fixed a Carrier furnace that had a broken damper motor on a zone.
Diagnosed a broken TXV on a Lennox heatpump.
Fixed a Goodman furnace that had a broken gas valve.
Replaced a broken thermostat. Unit is cooling again, and the filter is clean!
Performed a small maintenance on a Goodman Furnace. After the unit ran our crew left a few upgrade options for the customer. Everything is heating correctly with working parts!
Added a 5kw to a Goodman firdown. Everything looks good and both units are heating!
Swapped out the ignitor on a Goodman Furnace. No carbon monoxide is present in the home, and the filter is clean.
Fixed a Carrier heater that had a broken blower.