Diagnosed a Lennox AC with a leaking air handler.
Fixed a Trane AC that had a short in the thermostat wires.
Fixed an ac that had a clogged drain.
Checked an ac and made sure it was working.
Checked an ac and made sure it worked good.
Reaired an ac that had a leak.
Checked out an ac again and found no problems with it.
Fixed another ac that had ants stuck in it.
Discovered a leaky air handler that is losing refrigerant.
Fixed a broken unit woth a new capacitor.
Found a leaky evaporator that needs replacing.