airforce 1 do a fine job ,I have been using them for many years rick rock as a tech
The BEST technician!!
Great positive experience all around. My same day appointment was able to be pushed up and the technician, Dale, was very efficient, knowledgeable and friendly. Thanks!
Big fan of Rick. He is personable, educates me on the issue and the fix. Makes sure I don't have any questions at the end.
Overall great experience!
I have used A F One Air Conditioning for several years. They give me same day service their prices are reasonable.They are the best.
Replaced honeywell t-stat under warranty cycle system on and off 4 times all working fine
Installed new filter 16x25x1,replaced low capacitor on trane furnace to prevent failure of evaporator motor checked furnace all working properly.
Found defected compressor on trane conderser will send information about replacement of r22 3.5 ton system.
Technician Ricardo perform a warranty Mr Slim mini split heat pump Garage conversion application system blower wheel in door replacement due to a few of the blower fins had broken causing it to vibrate more finish it other than that system is operating just fine recommend a yearly maintenance to keep system up to manufacturer specs thank you again for your business
Technician Ricardo performed a new system heating check onto gas heating one closet and one attic application family closet application system burning higher than the attic system no carbon monoxide levels found inside the homes Airstream changed out all the air filters also all the heating and electrical components check out normal other than the age of the furnaces systems are operating normal now thank you for your business
Replaced old thermostat with a new Honeywell pro 3000 more efficient better accuracy of temperature
Technician Ricardo perform a warranty mr. slim indoor blower wheel replacement reset the thermostat control reprogram the time and set back to heating at 80� customer can go ahead and set who would ever comfort you prefer no other issues found system is ready for a cold winter and hot summer
Technician Ricardo and Aaron performed a trip and diagnostic on the rooftop carrier package system number 1 1 3 cleared out the main drain line that is also tied into unit 114 and eventually drains into the main restroom sink also recommended changing The blower belt and dirty filters and hope that's the reason the charging chart from the manufacturer recommend adding refrigerant customer declined and only accepted the drain cleaning will need to be taking care of the declined list now or later
Technician Ricardo performed and after hours service call only charge the service call but found a leaking gas line connection that was covered under the installation warranty but due to it being after hours I did have to charge a trip & service fee
Technician Ricardo and Aaron performed one preventive heat check on a rim attic application system replaced the week blower capacitor causing the motor to over amp no carbon monoxide levels found inside the home all other heating and electrical components checked fine other than bringing the gas line up to Code and air sealing the 6 connections on the supply plenum, also would recommend a digital tstat due to the old mercury tstat being very inefficient causing longer run times. Have a good day
Technician Ricardo and Aaron perform one preventive heat check on a Trane gas attic application system only found the hot surface ignitor with a few weak spots and went ahead and replaced before it totally went out also recommended air sealing all of the 30 - 50 metal connection joints on the ductwork due to air leaking into attic other than the age of the system beeing 16 yrs old & need to prepare for the worst unit seems to be working no other issues found at this time have a good day
Technician Ricardo performed a gas line fix after the gas stop in the upflow ring closet application system needed to take part and reseal the threads on the flex gas line too hard pipe going into the furnace cabinet tested for gas leaks. Tested heating and cooling to make sure they were operating no other issues found at this time. Full system install
Technician Ricardo performed diagnostic analysis on a Rheem 2012-2014 model upflow closet found the evaporator coil leaking refrigerant 410a the same goes for the service valves through the shut off on the outdoor condensing equipment recharged with refrigerant 3 pounds added will need to get a warranty change out of refrigerant leaking parts
Technician Ricardo performed a diagnostic analysis on a conventional gas r22 upflow in a closet system found a new nest thermostat cooling signal wire was not connected or making good contact so never was getting the air conditioning signal once everything was tighten back together performed The operation manufacturer test and specs nothing at of manufacture specs everything is running up to par other than regular cleaning maintenance and the age of the system its operating just fine
Technician Ricardo and Aaron replaced to Multi aqua heating element and a pair of blower wheels on one tested all the heating components and heating elements no other issues found system operating normally