I switched to AF1 after being ripped off by a previous company on several occasions. AirForce is extremely reliable and honest.
The techs (and in fact everyone I've dealt with) are always very courteous and professional. They strive to do a good job and keep their customers happy. And even if things don't work out as we all hoped (our outside unit turned out to be a lemon), they will make sure it is right in the end. That's a business culture others could learn from.
They are the perfect business to ask for a service.
1 system spring PM. Checked electrical components. Replaced air filter. Coils are clean. No issues or follow ups needed at this time. System is ready for summer weather.
Perform system maintenance talk to the customer about air quality improvements customer declined only recommendation at this time is air care quality improvements and separating the drains that are both tied in upstairs System is performing to manufacturer specifications at this time
Perform system maintenance no recommendations at this time customer was concerned about co2 detector in house co2 detector has 10 year battery life and is still operating will monitor the health of it as time goes on And recommend replacement when that time comes
2 system spring tune up. Checked furnace blower and coil. Checked duct work and drain lines. Replaced filters. Checked electrical components. Checked outdoor condensing unit. Cleaned coil with water. Checked refrigerant pressures. Checked fan and compressors. All electrical components check out. No issues found at this time. Customer paid in full.
system maintenance on all 3 systems talk to the customer about downstairs left unit having a dirty filter customer will proactively change filter in the future to avoid problem persisting other than that no recommendations at this time units were install 7 months ago Please see attached notes and make sure the following filters are on for the future tuneups 20 Ã— 25 Ã—4 x2 16Ã—15 Ã—4 Ã—1
Found leaks inside evaporator coil and condenser Send customer quote
Install new Linux furnace sl28ouh090v6oc
Heating Check up 2 systems both lenoox furnace are working great.
Prepaid furnace inspection 2 carrier systems both are new and working great..
Replace defective capacitor on main living area system 45+5uf refrigerant levels normal all working fine
Found leak inside evaporator coil will check for replacement asap.
Two systems maintenance tune up freon was added to upstairs system for better cooling both systems are ready for the summer
Cooling check of two systems york 10seer both are working properly.
Technician ricordo perform diagnostic on a gas carrier horizonal right furnace in the attic found the flame sensor faulty and needing to be replaced replaced it tested all other heating components to make sure no other issues were found everything else checked out fine is heating turned on just fine and cycled his thermostat off and on just fine should be ready for any more snow if we get any
Replaced 75 bolt hot surface ignitor on a Lennox system