Sam is doing a great job! Very happy with his work and customer service.
Efficient, professional and thoughtful
Samuel took his time to ensure the PM was completed properly, and explained in detail his findings! I hope Samuel remains on my home in the future!
Sam was on time, called 30 mins in advance, provided the proper tune up service, and fixed a problem we didn’t know was a problem!
Overall great experience!
This is the 3rd time I have used Air Force One and have been extremely happy each time!
I've been doing business with Air Force One since 1991, both at work and at home. They are great folks with great communication, always on time, very efficient, and trustworthy. I highly recommend Air Force One to anyone needing AC/heating service or new installation!
We have been using this service for years and have always been satisfied with them.
Always nice and does a good job
Called late Saturday, Rick came after 10PM the same night and quickly diagnosed the problem.
We've been using AirForce1 A/C for years, and never had an issue with them. Rick did a wonderful job with the A/C checkup, showed up right on time and was very courteous and professional. Highly recommended.
Ensure that system was working to manufacturer specifications recommendations as follows simplify duct network improve air quality and continue maintenance of the system please see pictures attached
Technicians arrived and taped and sealed supply plenum to upstairs unit with mastic. Supply duct collars were sealed with mastic at the joints. Joints of supply ducts are tearing at the seams due to the weight of the ducts and can be trimmed and reattached to prevent further tearing. During inspection found multiple leaks on upstairs and downstairs unit recommended replacing leaking components please see pictures attached
Condensate line rerun to correct drainage issues. Recharged coolant. System still not cooling due to deteriorated duct connections pulling attic air. Call with quote to fix.
Both in door units inspected. Drain lines found to be run incorrectly which is why no water was in drain pan. Far left 5 ton unit outside found to be significantly low on 410a. Dye pack and 410a input and lines checked for replacement
14 SEER 2 Ton American Standard Gas System Installation
System is working properly at this time
Technicians arrived and inspected evaporator coil in and found UV dye splatter. Condenser was inspected and found short on capacitor. Capacitor was replaced with new 45+5 capacitor and new wires were added and system pressures were checked. System is currently working and customer will be provided with estimates for new systems to review.
Replacing condenser and coil on Tuesday
Air filter replaced. Inside temperature within operational range. Inside unit and all electrical/duct work functional and im good shape. Outside unit electrical is also in good shape and operational standards. No defects or faults noted at this time.
1 system spring PM. Checked blower motor amps and capacitor. Checked temperature differential. Inspected drain line and blew it out and added Jones valve. Replaced air filter. Checked condensing unit. Cleaned coils with water. Checked electrical components. No issues found at this time. System is working as designed.
Talk to the customer about master bedroom system potentially having problems this summer customer understands and wants to wait until failure will address at later time systems other than that are working properly at this time please see photos attached
Condenser fan motor would seize up every now and then. Replaced motor with OEM motor from Gemaire. Ran tested system and it is working properly at this time. No other issues found.
Capacitor was blown. Replaced capacitor and tested unit. Pressures are good and 21 degree split. No other issues found at this time. Customer signed up for 1 year membership on 2 units.
1 system spring PM. Checked electrical components. Filter is good. Checked drain lines and duct work. Checked condensing unit. Motors are running good at this time. No issues found. System is working as designed.
Checked unit and it is cooling properly. 18 degree temperature split and pressures are good. No issues found. System is working properly in hot weather.