Overall great experience!
This is the 3rd time I have used Air Force One and have been extremely happy each time!
I've been doing business with Air Force One since 1991, both at work and at home. They are great folks with great communication, always on time, very efficient, and trustworthy. I highly recommend Air Force One to anyone needing AC/heating service or new installation!
We have been using this service for years and have always been satisfied with them.
Always nice and does a good job
Called late Saturday, Rick came after 10PM the same night and quickly diagnosed the problem.
We've been using AirForce1 A/C for years, and never had an issue with them. Rick did a wonderful job with the A/C checkup, showed up right on time and was very courteous and professional. Highly recommended.
Unit was tripped on low pressure switch. Did leak search could not find leak. Added 2 pounds of R-410A. Added UV for future diagnostic. Unit is cooling and heating at this time. No other issues found.
Will be returning on Monday with Warranty parts and problems should be resolved and will confirm and touch base with the customer the closer we get to that time Jim air plano is pickup location
Fix problems regarding unit shutting off told the customer to keep an eye out for any more suspicious behaviour from the unit
Unit was working when I got here. Tested blower and inducer motors no issues. Flames are coming out. Flame sensor is good. No issues found at this time.
Perform system maintenance ensures that system is working to manufacturer specifications
American standard system checkup
Talk to customer about new system 17 sear will reconvene before end of the month
Technician Ricardo and Aaron performed to preventive cooling checks found the upstairs condensing fan motor bearings going out customer went ahead and replaced water washed both outdoor units changed one of the 20 X 25 X 1 filters left the other one as an extra checked both the blower capacitors only needed to change the upstairs cap temperature drop across the indoor equipment at 20 degrees minimum is 15 degrees left a special order quote for the small details the inspector needed corrected
Customer has a cracked water reservoir that needs to be replaced on a lennox condenser furnace, will order part and return for repair
Heating Check 2system both systems are working great...
Replaced coleman hot surface ignitor that had cracked.
Heating check of one trane and one innercity product furnace. Tested for carbon monoxide leaks, none found, checked motors electrical and capacitors. Replaced upstairs 20x25x1 filter. Tested safeties and checked thermostat operation.
Trane heat pump maintenance tune up washed coils replaced filter checked refrigerant levels normal all working properly
Replaced low voltage 3amp fuse on carrier furnace
Heating check of a carrier and a trane furnace. Tested for carbon monoxide, no leaks. Tested all safeties, cleaned flame sensors, replaced filter and checked temperatures.