Super fast response on Sunday after hours. Guys cleaned the drain pipe quickly
Arrived on time and did an excellent job!
Kevin is conscientious and professional.
Great service. Very professional. Good price.
Thought the price of replacing the item was somewhat high. I dont.know what you all pay for it but I know a lot of factors are involved in pricing a item.
I am extremely happy with the service, price, and ethics. I was told by a competitor blower motors for my unit were no longer available and I needed a new unit for $2900. I called Air Force One for another opinion. They replaced the blower motor for less than $600. Thanks Air Force One!
Keven did an excellent
Makes me glad that I do business with them
They were able to get us a quick appointment, and the service tech diagnosed and fixed the problem quickly!
always a pleasure to deal with honest folks
I was a little suprised that such a major Trane component failed in less than three years. Glad that parts where still under warranty.
Response from Air Force One Plumbing, Heating & Air:
Thanks for the review! We love to hear praise from our satisfied customers. I will tell the install crew that you gave them a thumbs up.
Summertime HVAC Repair for a residential customer near Cullins Lake Pointe Elementary. Found pressure readings to be indicating low refrigerant. After a small amount added system pressure spiked to 600psi shutting off indicating a blockage in the line or metering device.
Replaced bulbs checked function.
Summertime Leak Detection Service for a residential customer near Mayor's Park. Found meter to be detecting a leak believed to be a slab leak Will arrange leak locate and write bid for repair
System preventative maintenance performed. Filter replaced in upstairs unit. The UV bulbs were operational however our replacement bulbs were not the correct ones. The upstairs unit had the compressor capacitor out of spec that was replaced. The unit is pulling over LRA with the compressor saver operating as it should and the customer was informed. Membership was renewed. Unit is operational and ready for summer
System preventative maintenance performed. Filter sizes were 14x25x1. The blower fan capacitor was out of spec and replaced in the downstairs air handler. Slightly high amp draw in both systems, customer was made aware and an estimate was sent for a compressor saver. Both systems are operational and ready for summer.
System preventative maintenance performed. Filter was sized 20x25x5 and needs replacement. High start-up amp draw was found with the condensing unit. A compressor saver estimate was sent and system is operational and ready for summer.
AC Repair for a residential homeowner near Waterview Park. System preventative maintenance performed. Filter was left with customer. Fan motor capacitor was found out of spec and recommended replacement. An Estimate was sent. System is operational.
Plumber for a residential customer near R. Arnold Edwards Park. Technician hydro jetted kitchen sewer line from outside clean out, clearing out debris. No stoppage was found at this time.
AC Service for a residential customer near Rowlett Nature Trail. System preventative maintenance performed. Filter replaced. Compressor pulling high amps, customer was made aware and an estimate sent. System is operational and ready for summer.
AC Repair Service for a residential customer near Cullins Lake Pointe Elementary School. System preventative maintenance performed. Filter replaced. All parts working as they should. System is operational and ready for summer
AC Service - Springtime HVAC Maintenance for a residential customer near Westwood Estates. Preventative system maintenance was performed. System is operational and ready for summer. Filter size 20x20x4 and was not provided this maintenance so two will be brought next time
AC Service - Springtime Air Conditioning Maintenance for a residential homeowner near Harborside Estates. System preventative maintenance was performed. Everything is operational and ready for summer. Condensing Units had a slight lean but were not detrimental to the health of the unit. Will observe any changes in the future.
Springtime HVAC Repair for a residential customer. Found upstairs system to not be cooling determined to be due to refrigerant. Customer will inquire about the warranty and let us know if they want to take further action.
Replaced warranty coil
Installed shut off valve on water heater in garage Tested for leaks Removed air from live water system