Arrived on time and did an excellent job!
Kevin is conscientious and professional.
Great service. Very professional. Good price.
Thought the price of replacing the item was somewhat high. I dont.know what you all pay for it but I know a lot of factors are involved in pricing a item.
I am extremely happy with the service, price, and ethics. I was told by a competitor blower motors for my unit were no longer available and I needed a new unit for $2900. I called Air Force One for another opinion. They replaced the blower motor for less than $600. Thanks Air Force One!
Keven did an excellent
Makes me glad that I do business with them
They were able to get us a quick appointment, and the service tech diagnosed and fixed the problem quickly!
Replace draft motor
Diagnosed bad motherboard blower motor and transformer talk to customer customer is going to find parts cheaper elsewhere and if not give us a phone call back
Inspected outside clean out for leaks. Found no leak. Ran water in upstairs fixtures. Replicated problem in upstairs front faucet. Unable to locate source of leak with camera. Referred customer to Berkeys
Inspected washroom sink, small leak from stops. Recommended replacing them on a later date. Customer reported washer lines not working. Inspected the lines and are now working. Small leak found on the hot water washerbox valve recommended replacement.
Replaced blower wheel. Ran tested unit and it is heating properly now. No other issues found at this time.
System was not cycling through heat. Inducer motor has a bad connection on one of the prongs. Will have to replace motor tomorrow. Was able to rig it to work for now. Customer will probably sign up for member tomorrow. Will take off difference of $139 diagnostic if they do.
Blower wheel became loose. Will replace wheel on Monday or Tuesday when part is in. System is working for now but is very loud.
Installed heat kit. 38 degree temperature differential. System is working as designed at this time. No other issues found.
No heat right side of house. Pressure switch stuck open code on board. Cleaned inducer port. Tested system and it came on. System is working properly at this time now. No other issues found.
Replace rough in inside wall by cutting portion of wall away to expose internal piping. Replace outer trim with customer supplied single valve trim kit. Difficult access.
Replace rough in inside wall by cutting portion of wall away to expose internal piping. Replace outer trim with customer supplied single valve trim kit. Normal access.
Plumbing estimate for two water shut off valves, 1 customer supplied sink, and 1 customer supplied shower trim kit
Ac not blowing air
Replaced old thermostat with a new Honeywell pro 3000 more efficient better accuracy of temperature
ONE SYSTEM PREPAID HEAT CHECK. TD-51 OK. FILTER WAS OK. LEFT NEW 20X25X1. Co INSIDE AIRSTREAM 0 PPM OK. Co GOING OUT FLUE PIPE 44 PPM OK. CLEANED OFF FLAME SENSOR. MOTOR AMPS OK. BLOWER WHEEL OK. ALL SAFETIES TEST OK. HEAT CHECKS OUT . WORKING FINE ON TEST DATE.