Logan was on-time, professional, cordial, and efficient. Overall, a very good service call. Thank You!
Response from All Seasons Comfort Systems LLC:
Thank you so much for taking the time to leave an excellent rating. We really appreciate your business.
Aubrey did a very good job. He was extremely thorough, and even spotted a problem that none of the other techs had ever noticed. Aubrey corrected it and explained it to me. Thank you, Aubrey! I will request you in the future when it is time for my service again.
Aubrey was very knowledgeable, cordial, and efficient. He understands what great Customer Service is, and delivered Overall a very professional, pleasent and effective repair experience. Thank You All Seasons Comfort Systems
Logan was great. He took his time and was very thorough. Great job!
Great as always !
They ARE very professional and courteous enjoyed having them in my house
Zachery did an excellent job explaining everything. Very thorough inspection and felt he was very knowledgeable with our heating products.
On time very knowledgeable
Very polite, and informative.
I called on a Saturday and they came on that Saturday. They fixed the problem and explained everything that needed to be done! The blending of professionalism with friendliness and a personal touch left me with an excellent feeling of complete satisfaction!
Planned maintenance a.c checkout on two lennox heat pump systems and 1 mini split. Both systems and mini split are showing normal operation at this time.
Doing a tuneup on a Lennox heat pump system.
Doing ac service on 6 geothermal heat pump systems.
Came out for planned maintenance agreement cooling tune up on a carrier heatpump. Found that the system was operating properly
Planned maintenance checkout on 6 geothermal heat pump systems
Came out for a no heat call found a bad transformer replaced the transformer and then found that there was a bad spot in the thermostat wire that caused the problem replaced the wire to fix the problem
Doing a tune up on a Lennox heat pump system.
Giving a bid to replace 60 feet of insulation on two supply duct runs in a crawlspace. Insulation was damaged during construction work. Repair solution would be to re-sleeve the two duct runs with new R6 rated insulation.
Doing a tune up on a Lennox heat pump system
Performing a planned maintenance agreement A/C checkout on a Lennox heat pump system. Washing washable filter. Washing outdoor coil and unit. Inspecting indoor coil and blower for cleanliness. Cleaning drain line. Testing system operation, checking refrigerant charge, temp split on evaporator coil, and electrical components. No issues found at today’s checkout of system.
Doing a tune up on a carrier heat pump and a Mitsubishi mini split.
Starting up new lennox heat pump system.
New Thermostat Installation - Setup and customer education on new system thermostat operation and settings. Also got customer signed up on planned maintenance. System working properly at this time.
Heat Pump Repair / AC Repair - Geothermal heat pump won't shut off
Heating maintenance on lennox heat pump system with washable filter.