Logan was great. He took his time and was very thorough. Great job!
Great as always !
They ARE very professional and courteous enjoyed having them in my house
Zachery did an excellent job explaining everything. Very thorough inspection and felt he was very knowledgeable with our heating products.
On time very knowledgeable
Very polite, and informative.
I called on a Saturday and they came on that Saturday. They fixed the problem and explained everything that needed to be done! The blending of professionalism with friendliness and a personal touch left me with an excellent feeling of complete satisfaction!
Giving a bid to replace 60 feet of insulation on two supply duct runs in a crawlspace. Insulation was damaged during construction work. Repair solution would be to re-sleeve the two duct runs with new R6 rated insulation.
Doing a tune up on a Lennox heat pump system
Performing a planned maintenance agreement A/C checkout on a Lennox heat pump system. Washing washable filter. Washing outdoor coil and unit. Inspecting indoor coil and blower for cleanliness. Cleaning drain line. Testing system operation, checking refrigerant charge, temp split on evaporator coil, and electrical components. No issues found at today’s checkout of system.
Doing a tune up on a carrier heat pump and a Mitsubishi mini split.
Starting up new lennox heat pump system.
New Thermostat Installation - Setup and customer education on new system thermostat operation and settings. Also got customer signed up on planned maintenance. System working properly at this time.
Heat Pump Repair / AC Repair - Geothermal heat pump won't shut off
Heating maintenance on lennox heat pump system with washable filter.
Heating system maintenance
Installing a Lennox heat pump system In a new construction home.
Installing a new heat exchanger and fixing exhaust and intake flues on a airflow gas furnace due to soot build up.
Heating checkout on lennox variable speed heat pump.
Heating tune up on lennox pulse furnace. Found system with intermittent furnace operation. Diagnosis- Found condensate drain backed up causing intermittent pressure switch failure. Soultions- cut and cleared condensate drain. Tested system operating properly at this time.
Planned maintenance heating tune up on amana heat pump system. System looks good at this time.
Came out for planned maintenance agreement. Checked system found no problems system operating properly.