Logan was great. He took his time and was very thorough. Great job!
Great as always !
They ARE very professional and courteous enjoyed having them in my house
Zachery did an excellent job explaining everything. Very thorough inspection and felt he was very knowledgeable with our heating products.
On time very knowledgeable
Very polite, and informative.
I called on a Saturday and they came on that Saturday. They fixed the problem and explained everything that needed to be done! The blending of professionalism with friendliness and a personal touch left me with an excellent feeling of complete satisfaction!
Doing a tune up on a carrier heat pump and a Mitsubishi mini split.
Starting up new lennox heat pump system.
New Thermostat Installation - Setup and customer education on new system thermostat operation and settings. Also got customer signed up on planned maintenance. System working properly at this time.
Heat Pump Repair / AC Repair - Geothermal heat pump won't shut off
Heating maintenance on lennox heat pump system with washable filter.
Heating system maintenance
Installing a Lennox heat pump system In a new construction home.
Installing a new heat exchanger and fixing exhaust and intake flues on a airflow gas furnace due to soot build up.
Heating checkout on lennox variable speed heat pump.
Heating tune up on lennox pulse furnace. Found system with intermittent furnace operation. Diagnosis- Found condensate drain backed up causing intermittent pressure switch failure. Soultions- cut and cleared condensate drain. Tested system operating properly at this time.
Planned maintenance heating tune up on amana heat pump system. System looks good at this time.
Came out for planned maintenance agreement. Checked system found no problems system operating properly.
Doing tune ups on 6 geothermal systems
Performing heating checkouts on two Lennox heat pump systems, and servicing a humidifier. Checking/replacing air filters. Testing emergency heat operations. Checking wiring and electrical components inside and outside. Checking refrigerant charges on both systems. Replacing humidifier pad and testing operation. Testing thermostat functions. And checking overall system performance.
Complaint of condensate drain line leaking. Found line to be plumbing water line, customer will have to get a plumber out