Always satisfied with All Seasons. Logan is pleasant and professional. So glad we have this company in our little community.
Super nice, very cordial and helpful!
Response from All Seasons Comfort Systems LLC:
Carrie, Thank you so much for taking the time to give Zach this great review. Zach is a great asset to our team, and is always striving to learn and grow. He is not satisfied, until he knows the customer is satisfied. It is great to hear when we are meeting the expectations of our customers.
Very nice and polite. Even drew me pictures to explain things
Zach is very thorough and knowledgeable. He is an excellent representative for your company.
I do a every 6 month check up and and it has proved to be a great way to identify possible issues and prevents unit performance outage.
Logan is a very polite young man. He took the time to explain the different checkpoints on our fall furnace checkup. Answered patiently my husband’s numerous questions. Logan is an excellent example of outstanding customer service for your company.
2 system heat pump heat checkout. Both systems look great at this time.
New install sensi WiFi thermostat setup. Got WiFi setup and went over app operation. System looks good at this time.
Performing a planned maintenance agreement heating checkout on a Lennox communicating heat pump system. Checking filter. Checking wiring. Testing emergency strip heat operation. Checking refrigerant charge on system. Testing outdoor electrical components. And testing defrost functions.
Performing a dual fuel heating tune up on a Goodman gas furnace and heat pump. Found gas leak immediately on gas valve. Shut off gas, re-sealed connection, turned gas back on, and then rechecked for gas leaks. No more found. Then completed system checkout on furnace and heat pump. No other issues found, system running properly at this time.
Troubleshooting a no cooling call. Outdoor unit not running. Found no 24v call at outdoor unit. Verified 24v from transformer. Found broken wire at outdoor unit. Cut back thermostat wire, remade connections, and tested system. System running properly at this time.
Planned maintenance checkout on Lennox High Efficiency Gas Furnace. System looks great at this time.
Performing heating tune ups on 2 Heil heat pump systems. Washing both washable filters. Inspecting blowers and coils. Inspecting all wiring. Testing backup heat/emergency heat functions. Checking system refrigerant charges. Testing outdoor electrical components. Verifying thermostats operate properly. And testing overall system performance.
Pma heating tune up on lennox heat pump. System looks good at this time.
Performing a planned maintenance agreement heat check out on a Lennox 80% gas furnace. Inspecting filter. Inspecting blower. Inspecting wiring. Checking burners, flame sensor, and hot surface ignitor. Performing a combustion analysis on system. And inspecting flue pipe venting.
Bidding new mini split unit and concentric vent kit.
Troubleshooting a noisy system complaint. No issues found on system. System was found being the loudest under defrost operations when the indoor blower is running the fastest. Provided customer education on system, and it’s functions.
Planned maintenance checkout on carrier gas furnace. System looks excellent at this time.
Planned maintenance heating checkout on lennox heat pump system. System looks great at this time.
Performing a planned maintenance agreement heating tune up on a Lennox dual fuel system. Checking heat pump charge and electrical components. Inspecting coil cleanliness. Replacing PCO kit. Performing combustion analysis on furnace. Inspecting burners, flame sensor, and ignitor. Inspecting glue pipe venting. And checking temp rise on system.
Complaint of system cycling on and off quickly. Diagnosis- Found blower cabniet insulation fallen down into return air, causing system to cycle on low pressure. Solution- repaired insulation with permanent metal holder. System is now showing normal operation.