Logan was great to work with, very knowledgeable, friendly and fast. Would recommend to everyone!
We’re able come come the day I called and fixed the problem quickly!
I was very pleased with the service and he is a very nice young man
I was kept informed every step of the repair process.
Logon was awesome and got us fixed within a matter of minutes!
Zack ran into issues that were unexpected, worked through them and over all, provided excellent service.
Zach was great and took care of our issue in avery timely fashion. He also was great explaining the problem and how he repaired it.
Came out to do a cooling tune up on a geocomfort geothermal heatpump. Found that one of the four zone dampers were bad. And found that the system was under preforming in cooling mode. Was able to dial the system in by adding water. Got the system operating properly.
Replaced 2 supply flex lines for homeowner due to water damage. System now looks good at this time.
Amana heat pump not cooling
Came out to install a low pressure switch on a lennox heatpump. Found that the switch was not working after changing Reversing Valve. Got the switch installed and made sure the system was operating properly.
Came out for reeheem system not cooling found start Capacitor and run Capacitor bad replaced them to get system operating properly
Performed a full cooling inspection. Checked all wires and safety switches. Unit is operating within factory specifications at this time.
Performed a full cooling inspection. Checked all wires and safety switches. Found outdoor sensor has failed. Replaced outdoor sensor. Perform safety testing. Unit is now operating within factory specifications at this time.
Customer education on thermostat operation and setup for remote access on new lennox heat pump system.
Came out to do a check on a napoleon heatpump. Made some minor adjustments to fan settings and checked the charge. System was operating properly.
Summer a.c tune up and cleaning on lennox heat pump system
Came out for lennox air handler making noise. Found that there was insulation in the blower causing it to be out of balance. Removed insulation and repaired cabinet to keep it in place.
Working on a Ruud ac unit that is not cooling dies to a leak in the indoor coil
Came out for goodman system not cooling. Found that the system was low on charge added r22 to get the system cooling.
Working on trane heat pump, thermostat showing error code 126 and 53.
Lennox heatpump not cooling. Found that the Compressor wasn't running. Due to to bad run Capacitor. Changed Capacitor to get system operating. Then check to see if system was operating properly. And it wasn't. Found dirty Condenser Coil and system low on charge. Washed Coil and added refrigerant to get system operating properly.