Zachary was very knowledgeable and explained the process along the way.
Got here on time, was very knowledgeable and got us fixed up w a new contactor and we are back up and running! Just in time for the heat wave.
Zach was very educational helpful kind great service
Zach did a very thorough job. He was professional and explained things thoroughly.
Your tech Logan was fantastic. Did a good job explaining the work he did and was very knowledgeable I had another company out and they said unit was just not big enough Logan found the problem and we are cool once again!
Our Service rep. Logan was very knowledgeable of the equipment and had no problem going out of his way to totally explain what was done and answer all our questions.
The HVAC tech (Zach) was great, very knowledgeable and attentive, explaining everything he was doing, which helped to educate me on the do's and dont's with my system. I have All Seasons saved to my speed dial now. I definitely recommend them.
Great job and kept me informed. Would have him again.
Logan did an amazing job getting our a/c working!!
Nice job good professional service man repair. Identified issue right away
Goodman system not cooling found bad run capacitor not letting compressor start changed capacitor and checked system it is work properly at this time
Planned maintenance checkout on Goodman heat pump system. System looks great at this time. See tune up sheet for more information regarding this service.
Troubleshooting a Goodman A/C not keeping up. Turned service call into A/C tune up. Washed outdoor coil. Checked indoor blower and coil for cleanliness. Checked both 16x20x1 air filters, filters were clean. Found system refrigerant levels to be off, and saw system showing over charged, reducing performance. Removed 8oz from system. Temp split went from 16-17 to 18-19 degrees. Opened a few supply vents that were closed off. Rest of system checks out ok with no other issues found.
Getting measurements on changeout on new system
Working on a Armstrong heat pump that is not cooling due to being oversized for the duct work
Complaint of water leaking under furnace. Found drain line clogged, also found both coils dirty and needing pulled and cleaned. Cleared drain line and tested. System is now draining properly and scheduled coils to be cleaned August 9th and tune up done on system after coils are cleaned. System showing normal operation at this time.
Replaced 51m33 thermostat out per Shannon. Thermostat was overcooling 2° Below setpoint. Replaced thermostat with new 51m33 and tested system. System showing normal operation at this time.
Complaint of black liquid looking substance under outdoor unit. Found system to show normal operation and that black was just mold/mildew on pad.
Pma a.c checkout on lennox high efficiency heat pump system.
Came out to find out why a train system was tripping the breaker. Found a bad breaker and a bad compressor.
Came out to find out why a system wasnt cooling found the system freezing up due to being low on refrigerant. Recommended adding refrigerant to find leak but with age of system customer decline repair operation in favor of replacement.
Ac outdoor unit not shutting off found contactor stuck had to replace contactor system shutting off when supposed to
A.c checkout on lennox heat pump system. System looks showing normal operation at this time. Recommend annual maintenance.
Planned maintenance on Lennox system all in good working condition
Planned maintenance checkout on lennox high efficiency inverter heat pump system. System checked out excellent at this time.