I AM REALLY THANKFUL FOR AUTUMN AIR. THEY ARE TRULY A BLESSING...GREAT SPIRIT, CUSTOMER SERVICE, PROFESSIONAL ACROSS THE BOARD. I TRULY & HIGHLY RECOMMEND AUTUMN AIR!!!
He replaced the bad part and our home started cooling right away. Next day it was making a noise and they set appt to be here within hours but the noise stopped so we called to tell them. Hopefully it will do fine but they assured us if any problem just call. Thank you for your service
This is the second time I’ve used Autumn Air and both times they did a great job at a great price. I would highly recommend them to any of my friends and family and do!
Would have been better if we weren't paying $150,48 for returning the faulty part AND another $386.95 for the loss of coolant during repair
Technician found a few things that needed attention and immediately took care of them.
Very professional and knowledgeable.
Called in with a no cooling. Baker went out first call this morning. Replaced the capacitor and got the unit back up and running.
Had an older system that wasn't cooling. We installed a new Amana System for them.
Needed a new system for the home they just bought. We got them a new Amana system installed at a great price.
Had a very old system replaced their old worn out unit with a new Amana System.
Richard arrived to find he had a bad coil in the airhandler on unit. Worked with the Home Warranty and got a new one installed
Autumn Air precision tune up also changed filters this visit.
Arrived to find a bad capacitor on unit. Changed out capacitor and got unit back up and running.
Called in with a condenser fan not working. Arrived to find out the fan was the issue and replaced the fan and got them back up and running.
Arrived and performed a Autumn Air Precision Tune Up
Unit had poor cooling went out and diagnosed the issue. Someone before us had replaced the control board and motor the unit also need refrigerant.
Called in with unit not cooling got it back up and running and also did a maintenace
WENT OUT TO DIAGNOSE WATER LEAK AND PROBLEM WITH SYSTEM.
WENT OUT TO DIAGNOSE WHY UNIT WAS FREEZING UP.
WENT OUT TO FIX NO COOLING ISSUE ON UNIT.
WENT OUT TO DO A FREE SECOND OPINION.