Bay Area was very helpful when our air conditioning system began to fail. They even came over at night to fine tune it. What a GREAT company!
The technician was very professional, he was thorough and knew what he was doing. Second time we’ve used this company
Had had another company put in my air conditioner last year I would not give you $0.02 for them they were disrespectful did not honor the warranty will not come back up to Citrus County now after they put in the unit they're out of Hernando their name is are Associates will not help in any way shape or form after I call them about the leak again that just happened in 2020 that happened in 2019 after it was first put in I had at least a dozen call backs to them for issues within the first two months of it being put in call Bay Area they took over they've been nothing but wonderful I have nothing bad to say about them I called and they were here within an hour and a half to fix the problem told me how to maintain the problem have nothing bad to say about them anybody that's looking for an air conditioning company I would definitely choose Bay Area
Appeared knowledgeable and explained what needed to be done.
Only complaint we have is that the answering service thought we were in Beverly Hills California. May want to inform them that we are in Florida.
Mike Barry knows what’s he’s doing and was a life saver. He’s the best!
Checked operations of unit found drain line clogged uncllogged drain line. Unit is running normally at this time.
checked operation of unit. Found run capacitor bad for compressor. Changed out run cap. Unit is running normally at this time.
Found no refrigerant in the system and a leak on the liquid line inside the condenser. Explained to customer how much would be to fix it, recommended to replace the ac system. The $30.00 off per Martha.
Check the operation of unit. Found that blower wheel had sunk into bottom of housing. Looks like previous installers of blower wheel did not tighten key tight enough. Blower whrel also looks to be wrong size for this particular unit. Unit is running normally at this time.
Checked operation of unit, cleaned unit, unit is running normally at this time.
System off on float switch, Very tight Attic, Vacuum out drain line with wet vac, drain is trapped outside, Better way would be Trap and vent at AH, I did not have room to move in attic, Did not get hose up there tp flush, Has a 9C scheduled in a few weeks, Removed locking caps that use the small Allen wrench, Checked pressure, Thank you
Checked operation of unit, found drain line clogged. Unclogged drain line. Unit is running normally at this time.
Annual service clean and check system, flush drain. Replace UV bulb and filter, system operates normal
Tightened brass service caps & added refrigerant, checked operation
Indoor unit icing up customer allowed unit to defrost. Jumped out indoor fan and ran, outdoor unit came up and ran. Discovered indoor fan relay board in attic cutting out intermittently. Replace board with relay due to dampness.
Mark breakers properly
Found low voltage fuse blown Trace short back to thermostat replace thermostat also found bad moisture sensor replaced with mechanical float switch unit working properly at this time
Find float switch tripped flushed drain line drain pan unit draining properly at this time
Found drain line not draining properly flush drain line drain pan check system unit working properly at
Found compressor lead blown off compressor all refrigerants gone Lyft estimate for new system not sure of tonnage