Look forward to doing service with them.
Was amazed at the quick response I got from Bay Area Air Conditioning
They come when they say they’re going to come and they assess the problem quickly. Reasonably priced as well.
Jaime was knowledgeable, informative and friendly. Highly recommend!
Outdoor fan not running, Found open Dual run Cap, Replaced capacitor, Tested System, Up and Cooling Thank You
Compressor runnings but not pumping correctly, wont pump down at all, sent info to parts for quote
Started raining need to come beck
Call back obvious drain problem. Float switch and primary drain are at the same level repipe float switch so customer could empty drain should problem reoccur. Flush drain and checked.
No indoor blower check for correct call order new module. 1/2 hp. Evergreen possibly
Other AC company replaced indoor fan relay, they appear to have done a good job doing it, they told her the 15-year-old system is in decent shape and running, I agree with that analogy, average life of the systems run 12 to 14 years, however this one is cooling and draining water fine at this time, Call is a free second opinion Thank You
System off on Float Switch, Reset, Flushed out drain line, Attic, Cooling and draining water at this time, Thank you
System tripped out on float switch flush drain and pan check system operation, function is normal.
Found drain line clogged flush drain line and drain pan vacuumed out secondary pan unit draining properly at this time
Install surge protecter, PO#10289ol
Found float switch not set correctly drain line clogged flushed drain line drain pan added condensate tabs and Dawn dish soap
Replaced blower motor
System operating, check Delta at evaporator 77 degrees inside. Clean coil and blower, replace blower capacitor. 23 year old system quoted Outdoor Motor and new system
Replaced motor module system operating correctly.
Customer called due to system not operating correctly found system to have a completely compacted condenser coil. Cleaned coil with water hose and checked system operations in cooling all ok. Recommend system getting a maintenance also spoke with customer about hosing condenser coil off periodically. System operating and draining correctly at this time.