Steve is an experienced service guy. We always ask for him because he is thorough, always finds the fault and gives good advice.
He was here shortly after we called and pumped the water out. The air wasn't shutting off so Bill called him and when the air shut down we were able to let him know it was okay. Very helpful.. We are from Wisconsin, so are just learning about this type of air conditioning.
Compressor quit working on our A/C. Repair technicians were able to replace our compressor the same day as called.
Service was great, no complants, wish there was a senior discount or a Vets discount
He is a very nice technician and explained everything for me to understand
I have been a Bay Area customer for twenty two years and have always been treated with respect. The technicians are knowledgeable, professional and extremely helpful. I give them a ten start rating!
I HAVE BEEN DEALING WITH BAY AREA AIR CONDITIONING FOR 28 YEARS. IT IS A GREAT COMPANY TO DO BUSINESS WITH. DALE FRASE IS THE BEST. HE IS A SUPER FANTASTIC TECHNICIAN. WE ALWAYS ASK FOR HIM.
Adjusted drain line on attic Trane heat pump 4 ton
Repaired Carrier Brystal Compressor AC
Replace bad contactor and a 4-ton Carrier split heat pump for one of our many valuable customers in Homosassa Florida
Air conditioner repair three-and-a-half ton Carrier heat pump moisture sensor
Flushed out drain line, to old Tempstar AC 3 ton system
Repair indoor blower on a 3-ton carrier packet split heat pump for one of our many customers and Sugarmill Woods Florida
A/C Service on Carrier 3 ton air conditioning system. Replaced capacitor and verified proper operation.
Air conditioning diagnosis 3 ton Carrier heat pump thermostat
AC repair 3 & a half ton Carrier heat pump drain line
Leave quote to replace 3 ton package unit with new efficient carrier 3 ton package heat pump for one of my many valuable customers and Crystal River Florida
Flushed drain AC drain line, added dawn, Trane high efficiency heat pump
A/C Service on 3 1/2 ton air conditioning system in Dunnellon, Fla. Replaced indoor blower motor module and then verified proper operation .
Diagnose bad and leaking accumulator on a 4-ton Carrier split heat pump. New part ordered and will be repaired very soon
Air conditioning repair 3 ton Carrier heat pump Transformer
Replaced old Carrier 3 ton heat pump contactor AC