techs that installed our unit did a find job. not messy, they where excellent.
Keith is real good asset to Bay Area. Thorough and very courteous.
Shane was very good at finding the issue with the system set up and fixing it.
Everyone that I have dealt with, from the office personnel to the installers were great. They were very professional and exceeded my expectations, after being referred to them by my home performance specialist.
Shane came out and was very personable and knowledgeable and took the time to answer all my questions and concerns. I was very satisfied with everything. You have a new customer. Thanks for the great customer service.
David’s a great tech. You can count on Bay Area to be truthful and honest...they don’t sell you on stuff that you don’t need.
Bay is the best we have had in our 17 yrs in Ocala. Bought top of the line unit and they keep it like new. Courteous thorough servicing. Great office reception. Recommend to all. Always there to answer my questions.
As always, very pleased with the service you provide.
An excellent company from my first call to Lisa with my concern to the gentleman that came out to look at our unit they had installed a cpl years ago. Excellent equipment, fantastic service. I highly recommend them not only because of their products but because they work with the customer and actually want to satisfied them.
We have been using this company since 1991 when we built our house. They are very reliable and their techs are always very nice and do a great job.
Same day service even though they came from another county. Both servicemen were proficient at solving the problem. Had hoped the service contract would cover it all seeing the unit is only 2 years old, but overall, satisfied with the job they did finding what the problem was.
This is An Estimate to Install A New Carrier 17.5 seer Five Stage Heat Pump. With A 10 Year Part and Labor Warranty.
System operating and functioing properly at this time.
New system for guest house. Will need breaker panel information for install.
Check up complete continue yearly maintenance thank you
Annual service clean and check system, flush drain. System operates normal
Annual service clean and check system flush drain. Drain clogged condenser very dirty instruct Mr operates normal
Found the failed blower motor. The customer is buying a new system, so installed the temporary blower motor, customer paid the safety deposit as a partial payment for the new ac system.
Out in aug 2021 to check up and unit tripped on float switch charged diagnostic but did not charge for drain cleaning only been 2 months
Blower came apart inside squirrel cage. Replacement of motor and blower. CCW mounted on right.
No communication to infinity blower motor, Replaced infinity blower motor, system operating and functioning properly at this time.
Check up complete continue yearly maintenance thank
Clogged drain. Blew out and checked system. Operates normal. 2.5 ton Lennox
Found water in float switch Flushed drain line drain Pan unit is draining at this time
Low suction low subcool. Adjust charge less than 1 pound. Had change in subcool, check unit air flow blower would not ramp up and very little static. Order new blower and recheck charge.
Customer did not answer, left message.