Checked over the system to find biological growth within the air handler. The system is r22 and 17 years old. Recommend having it replaced before Offered 12 months no int financing.
Completed the maintenance inspection
Found blower luckily stuck in on position at moment no matter if there is a call for heat , cool , or off. Need new motor and module. Possibly has a part warranty. Not one of our installations. Note has heating at this time also customer to be billed
Replaced 5 kw heat package with broken terminal block. Restarted and tested cooling.
16 SEER 10 YEAR PARTS AND 1 YEAR LABOR
Found the system a little low on r22. Adjusted the superheated from 31 to 14degrees. 64 degrees coming from the supply vent. Vacuumed the drain system. No charge. Customer is having a new system installed on 9/30/2020
Rewired thermostat and replaced weak run capacitor in outdoors Noticed that outdoor unit is R22 freon and indoor unit is designed to use 410a refrigerant. This is not the best match. Customer will call in payment