We checked Reme cell and retreated with peroxide. We quoted moving a duct. Homeowner going to run system and let us know if smell goes away. Quoted 200.00 to move duct.
Customer concern was no heat. Upon arrival noticed system Indoor and outdoor thermostat only have 4 wires. Heat strips are not wired. Running only 1st stage heat. Informed unit will struggle to maintain heat durinng cold night. Quoted to replace indoor and outdoor thermostat wire. Unit is running at this time. 90â° coming out of vents. Emailed bill and quote.
Completed the maintenance inspection. Replaced the media filter
Completed the maintenance cleaning on both head units.
Checked over the system to see if I could find the source of the odor. I went ahead and sprayed the air handler and return box with Hydrogen Peroxide and wiped down the blower wires.
Ran system, system was at 50psi got system 75psi and ran out of 410a did not find leak outside needs leak search done inside
Completed the maintenance inspection. Recommend treating the drain line everything the filter is replaced.
Found a clogged drain line. Flushed, treated, and tested the system.
Found a bad blower motor. Check into the warranty it the system isn't under a warranty under the last name Velez.
Cleaned drain line and coil pan treated with viper and dawn dish soap. There is a 3 90Â° coming down outside causing another trap we can strain in and only use 1 90Â°... Call back? On drain line. No charge
Found drain had backed up and shut system off. Water had cleared but float did not completely reset. Reset float and cleaned and flushed drain. Treated drain and primary pan. System is now draining properly . Customer will be calling office with payment
Completed the maintenance inspection. Replaced the suction line locking cap.
Replaced the defective evaporator coil, TXV and drier. Added 6 lbs of 410a Found that the system was pumping down after the install due to a bad expansion valve. Will need to order and return.
Found a bad capacitor. Replaced the capacitor and checked the 410a pressures. 142/295 with a 8 degree Subcooling
System maintenance on heatpump system . Spoke to customer. Credit card is on file.