Don did a great job he is an asset!
Bay Area service person quoted me 2K for a “bad” compressor replacement. Or, 6K for a new system. Or 14k for a super great system! Very reasonable I thought. I thanked him and told him I would get another estimate and compare the two. The next serviceman from a much smaller company showed up in an old van that was probably paid off 10 years ago and needed a good wash. Anyway, don’t judge a book right? Young guy actually. He looked at the unit, did some tests and said, “there is a wiring problem. You need a new harness and I think I can get this compressor going.” He went back to his van, got a new harness and installed it. Bam. Done. $188.00 and he was on his way to the next happy customer. Incredibly important to get at least 2 estimates.
Robert has been coming annually for a number of years for the annual check & service. He is always great.
Great service, efficient, friendly and knowledgeable.
Everything explained well.
Friendly professional staff
We have a weekend home and I went over Today to check everything out and found the air conditioning not working. I called Bay Area Air Conditioning and they were there within the hour. Did the diagnostics and found the problem quickly. Parts had to be ordered but I was called this afternoon to approve the parts purchase and quoted the price for parts and labor. Our technician Mike was professional, knowledgeable and explained everything with patience. I highly recommend this company!
Went..over options with customer. Not going to buy a new system at this time. Maybe calling in to have blower motor Replaced.
Blower motor bad left estimate on blower motor and left estimate on infinity system Customer would like estimate on multi-head mini split and possibly of putting a package unit in ductwork up the side of house will have sales and construction supervisor to come out and estimate on Monday
Ms says scheduled for next week. Weekend renters in house. Was able to get in garage and replace 6in of rubatex. Sent photo to inspector. Also light cover fell and broke after technicians left owner will call, see photos. Photo of repair was sent to inspector
Found bad 10 KW heater heating element string broken fuse link blown replaced heater under part warranty only test it normally at this time, parts to leave courtesy estimate on 15kw heater
Found dual run capacitor bad on system still would not start discovered that windings on compressor or bad put a new equipment and replacement of compressor. Homeowner will discuss with their spouse and decide what they want to do
Home inspector stated heat pump leaving are temperatures different coming out of each vent. Started heat pump and ran. Check refrigerant charge system charge is fine. Upon startup indoor temperature was 58 degrees Fahrenheit. After running for about 10 minutes. Leaving air temperature was approximately 102 degrees. Leaving air temperature on unit with heat strips went to 113. House did warm up to 64 degrees while I was there and leaving air temperature increased accordingly to 107 degrees. There is a variance of 2 to 3 degrees I mean out of each vent. This is normal. System is operating normally at this time
customer had to leave reschedule
Checked insrall homeowner had questions and to see if return plenum was supported correctly it is a long return plenum and there is three supports under plenum explained to homeowner that is needed to support plenum
MECHANICALLY CLEANED INDOOR AND OUTDOOR COIL. FLUSHED PAN. VERIFIED ALL AMP DRAWS AND ELECTRICAL CONNECTIONS. WILL RETURN ON A WARMER DAY TO VERIFY REFRIGERANT CHARGE.
Replace broken controller cool button broken,system running normally at present time
Unclog drain line unit draining into emergency pan emergency paint is rotted out instruct customer this may still leak suggests new equipment will have sales and construction supervisor to est
Customer complaint of no heat. Found indoor blower motor running but no electric heat. Electric heat kit relays not energizing with call for heat. Replace with 2 pole contactor in place of small cat relays that energized heat kit. Unit is operating normally at this time. Unit under 10-year part warranty. Don't forget diagnosis in labor
FLUSHED DRAIN LINE. UNIT WAS SET TO 90 DEGREES HEAT. HOUSE HAS BEED DESTROYED BY PREVIOUS RENTERS. ADVISED WE WILL CHECK UNIT 8 AM CALL. WHEN HOME CLEANED UP.
Found bad Transformer and fan control board homeowner thinks she may have a parts warranty