Checked over the system. Found the Subcooling low which would cause the system to freeze. I also found a bad blower relay which is causing the blower to run all the time and the electric heater is running due to a bad heater relay. The customer has a January electric bill of $609.47 and a December electric bill of $432.76 The system is 15 years old and in poor condition. I'd recommend having the system replaced.
System maintenance on heatpump system.
Found that the condensation isn't coming from the ac system.
Found the system had the breaker off and a dead frog behind the AOC board. Reset the system to find error code 48. Loss comm. With inverter. Recommend replacing the inverter and control board. Will place the order today.
Service call completed, upon arrival check electrical components, found blower run capacitor open, replaced defective component and check refrigerant pressure, system check out low of refrigerant, charge 3 lbs of refrigerant, performed a quick leak search and no leaks found at the moment, advised client system condition, unit is 9 years old, there is some areas impacted with rust , systems aren't in warranty , send a free quote for system replacement in case client want to upgrade for a better efficiency system financing options are available , both systems are operating at this time
Found that the disconnect was pulled from the air handler. On the earlier visit today they must of forgotten to added the disconnect. Serviced the drain line and checked the systems operation.
old breakers match new system none needed
Ran complete system tune up. Found a short at A/H and fixed it. Found no other problems. Static was at max for duct system. Cleaned drain and coils. Treated coils and drain. System Orting within specifications.
Ran complete system tune up. Found no problems other than drain being plugged up. Cleaned, flushed and treated. Blower is clean and evaporator is as well. Checked all other factory specifications and found no problems. System working good at this time.
Service call completed, upon arrival removed air filter moderate impacted , check system operations, noticed dual capacitor was improperly wired, changed and tested equipment, system going to soft locks put due a low pressure into the evap coil, meter device need replacement, advised clients system condition and provide with options and recommendations sedn to the email on file , call clients when part are available
Found a bad blower motor. Fault code 44. Replaced the blower motor and tested the system.
Service call completed, system up and running upon arrival, check electric components and refrigerant pressure, system is within the manufacturer specification, advice client if problem persist call us with a active code for a further diagnostic
Blower wheel put of balance, advised to replacing the blower wheel may ease up the unit vibration but is not guaranteed, client want a quote for blower wheel replacement
Service call completed, package unit over 20 years old, multiple issues and deficiency ,heavily rust and impacted , advised tenant about system condition, strongly recommended to replace air conditioning, financing options are available