My experience with this company is very satisfying!! The response time is beyond expectations!! They did not quit unti they were able to troubleshoot my heating issues and fixed it.
Excellent and Professional service.
Called and had the job done in less than 2 hours!
located problem and remedy very quickly.
Mark and Bay Area are outstanding. Great experience.
Matt was the technician that worked on the air and heat and did a very good job. He found the problem and we are good to go. Thankyou. Larry. Dobiak
Great service and very informative to get our unit working
Sysdown and out , sedn parts Order quote for heat element, thermostat, blower motor, both unit are 10 plus years old, no warranty on units, call client with complete quote for system repair
Found that outdoor sub panel is beginning to melt behind breaker. And suspect new thermostat will need to be pulled under house. Will need daylight and two techs to do this. Possibly will need to change thermostat also. Need to return during daylight hours.
Recall. Removed jumper in outdoor unit that was causing system to run in cooling regardless of thermostat setting . Tech 930 corrected thermostat configuration yesterday. Jumper was possibly left on by tech from previous company.
Fou d straight cool with 10kw electric heat package unit operating properly in heat. Breaker tripping after a few minutes of operation. System fed with #10 THHN wire and no service disconnect. Cannot read mca or mop on unit label anymore. Reccomend replace wire from panel with circuit of at least 6 thhn or 4 romex to new service disconnect and then appropriate whip into system.
3 ton system, (strt cool) Improper tstat, (heat pump) Noisey breaker identified as for Indoor Unit (30a with #10 wire) Indoor unit with heat on draws 33amps, the breaker in question is going into failure, breaker panel appears to be a 60 panel, tenant has been instructed to NOT USE heat until electrician is on property
Canceled call. Maintenance moved a unit from a unused space to apartment #331 I did no work on system or anything.
Moved hurricane clamp from access panel to center front of machine marked heat strip size mark breaker for AC and breaker panel unit ready for reinspection
2 ton heatpump system at least 11 years old. R22 freon. Replaced open fuse link that allowing electric heat package to turn on to aid heatpump in colder weather. Tested heatpump and checked freon. Was unable to test defrost due to high outdoor temperature. Left quote for new system due to age 9f current system. Electric panel must be upgraded before any installation of new system. Part number SL075B
System very load tested duct pressure .97 total need to put in turning viens in supply and return Pete cannot do this after turning veins are put in they want me to come back and just set up the system and explain it to them please set up ASAP
Tune up complete Replaced infinity air filter
Upon arrival the stat was in lock mode and homeowner did not know how to unlock it. I unlocked stat and explained all functions and what buttons to push and what not to push. She is only going to run heat or one function at a time instead of auto.
When arrived checked system in heat. Found air handler blower and electric heat running but heat pump not running. Found no call for outdoor unit from thermostat. Verified configuration and found tstsat configured for straight cool operation with electric heat only. Reconfigured thermostat for correct equipment type. All operating properly now.
heating element need replacement, parts Order request form send it to proper channel , call client when part available
4 ton HP with dehumidification AH and thermidistat.
Replaced Infinity blower motor that would not communicate with system. Restarted and tested new motor and heating. Warranty