Cliff was very knowledgeable and explained to me what tests he was doing and also what the results should be.
I’m happy with the company because the quick response and technicians professional service. Thanks Bay Area
Good service man
I was giving a great price and they were so professional. They installed a brand new AC unit for me and it was an Amazing experience from star to finish.
Jeff is an asset to your company.
Came in immediately detected the problem had everything ready got it changed out in a matter of minutes
Found the system off on float. Removed the water from the float reservoir and flushed the drain system. Note: found a lot of water within the air handler. To find out from the tenant that the landlord used the garden hose to run water from outside in which would have caused this issue.
Found nothing with thermostat that looked off. Temp was set at 82Â° and humidity at 55% . Temperature was 82Â° and humidity was 55% . Checked with my Fieldpiece thermometer and it was at about same reading. Within a couple % and 1 degrees
Found blower motor locked up and system out of refrigerant. Not worth fixing
On arrival found the system frozen over. Defrosted the system and found the unit low on 410a. Added 4 lbs. Found some oil at the condenser coil. Recommend having the system replaced. We will credit today's visit to the install. Office to call the customer to set an install date.
Service call completed, upon arrival, system was working properly, check system operations and refrigerant charge, unitbis operating within specifications, client stated after they changed the air filter , the unit started to cool down the property , recommended to replace air filter regularly and upgrade thermostat
10 year parts and 1 year labor warranty
Found the system low on 410a. The customer is aware of a leak and has the house up for sale. He would like to get the system gases up and running again. Added 5 lbs of 410a.
Upon arrival I went to rooftop unit. System was very old and labels missing. I removed panels and found it iced up. The blower motor was not running.,I checked amrad capacitor and it was fine. I checked wires to blower motor and found one broken off at the contactor. It had dry rotted the terminal. I replaced terminal and fan started. I shut system down and kept running blower. They are going to keep system off till morning. I warned them of possible water dripping on ceiling do to ice melting. We discussed new units and wants to add a new. He is going to have Jim Horton come out.
1 year parts and labor 5 year compressor warranty
System low on charge, compressor making tinny sound. Adjusted charge, noise went away.
No answer ph, no response to message after 20 min, need RS
Compressor was initially overheated & reset quickly during capacitor check Compressor drawing 139 LRA, windings ohmed out as well as minute reading to ground, windings insulation integrity loss Although capacitor seemed to test out the start line had no current draw Replaced capacitor & tested Also vacumed drain at outlet
No cool, check and replaced dual capacitor. System operating at this time. Warranty
Replaced shorted dual run capacitor. Restarted and tested cooling and checked puron level.
Found system at 11Â° TD Checked charges and found them off on sub cool by 5Â° Added 1 lb 410A system calls for 10Â° sub cool. Now sub cool is at 10.9Â° TD Is as 15Â° Did quick leak search and found none.