Glen was the most knowledgeable of all your great techs I have dealt with. I’ve got my fingers crossed that the problem is finally fixed.
Once again, I’m very satisfied with the service I’ve received from Bay Area A/C!
We have had an ongoing refrigerant leak in our air conditioner, one that is very hard to pinpoint. Jeff has done a very diligent job of trying to locate it, and we’re both hoping it’s finally fixed. As a retired tradesman who has extensive refrigeration experience myself, I really appreciate his commitment and skills.
Through no fault of his, this is the second time Jeff has had to service our A/C this year. Both times he has demonstrated conscientious professionalism in approaching and taking care of the problems. He has consistently explained what was wrong and his solution clearly. As a retired service technician myself, I recognize good service!
I got a quick response to my problem. The technician, Jeff, was quite knowledgeable and personable, solving the problem quickly, explaining it clearly, and all at a fair and reasonable price.
Cliff was very knowledgeable and did a great job explaining what was going on.
He was very professional and polite.
We always ask for David
Arrived within time limits, polite, clean and fast.
We have had David for 4 or 5 years, I ask for Dave ! He always is enjoyable to have for our service work. I will expect to have him as long as we live here.
Flushed, treated and tested the drain line. Customer is getting the new system order and installed soon. No charge.
10 year parts and 1 year labor warranty
SYSTEM NUMBER 5 Replaced shorted dual run capacitor and cooled down compressor that was over heated. Restarted and tested cooling.
#3 rooftop unit on SE corner Evaporator 50% frozen solid, blower belt flopping. Sprayed rust blaster on adjusting nut. Unit suspect of low refrigerant = refrigerant leak Return when unit thawed to confirm, possible leak search
Customer canceled at the door.
upon I removed 3/4 hp module and installed my temp module. I collected 200.00 per Dale to be credited to new equipment. It is cooling at this time.
Bryant 288ANA036000DBAA. 1709E21021 Replaced outdoor defrost board that had signs of corrosion and burn marks. Rebooted and ran install. System is running now. Customer supplied defrost board. May need to replace model plug Recall.
Leak search, found leak hot gas connection to S/O valve (confirmed with soap bubbl) 125psi standing in system, removed refrigerant, solder repair at leak, pressure test to 325, changed drier, evacuation, restart & recharge with virgin 410, recorded stats
Replaced contactor with pitted contacts . Restarted and tested cooling. Checked freon level
Found that the blower motor is fading in and out. Replaced the blower motor and tested the operation.
CLEANED AND FLUSHED ALL THREE SYSTEM DRAIN LINES. ADDED DRAIN TABLETS AND VIPER PAN SPRAY. RESTARTED AND TESTED ALL DRAIN LINES. QUOTE FOR NEW AUXILIARY FLOAT SWITCHES $144 PER SYSTEM.
Found a bad blower module. Need to order and schedule to return.
System low on charge, recharged system. Tried to perform leak search. No leak detected but evidence of oil at and near distributors in outdoor unit. Need to schedule tech with good leak detector to return, leak search and repair.
Verified that contactor coil was not shorted. System was running upon arrival. Replaced defrost board. Customer supplied used defrost board as the replacement board. Ran full install on main controller. No warranty on new board
The customer was in the attic and the low voltage wire leading from the air handler to the thermostat came apart. If this problem continues I would recommend having it replaced. After fixing the issue. Completed the maintenance inspection.