Cliff was very knowledgeable and did a great job explaining what was going on.
He was very professional and polite.
We always ask for David
Arrived within time limits, polite, clean and fast.
We have had David for 4 or 5 years, I ask for Dave ! He always is enjoyable to have for our service work. I will expect to have him as long as we live here.
Quickly identified the problem and explained what would be the solution. Always great service from Bay Area and Robert was in step with what I expected.
Even tho it was the first hot spell of the season, Bay Area A/C didn't stop until all their calls were done. The office reassured us that someone would be here today and Glen showed up and fixed our problem.
He has been here 4 times,you have A great employee with David
Checked electric heat elements and verified they are working. Tested heatpump side of package system. Wired system so electric heating elements will turn on with heatpump Auxiliary heat when needed. Air temperature at air vents with both heatpump and aux heat was 116 degrees.
Only 1 access to the roof requires 2 ladders and 2 techs. Decline service per John.
Testing concluded ID Unit control board not communicating correctly, refuses to ID indoor Replaced with correct board and now controller IDs as different model, however does ID system size and testing shows air flow at 1207cfm Contacting Carrier for verification of certain results currently existing , per customer request old board left on property
Completed the maintenance inspection. No recommendations at this time.
Assisted Dave with pulling wire
Installed standard thermostat at customer request to getmsystem working . Need to return to replace thermostat wire under house . Will need two techs. Cost time and materials. Used TP N 621 Collected $251
System number 2 Replaced thermistor sensor kit. Tested cooling Collecting 2 diagnostic fees on this invoice for other system.
Checked system and found that model plug chip in outdoor unit showing improper resistance and not recognizing right size system at wall control. Need to order chip HK70EZ 010 BRYANT 288ANA024000DBAA 1609E12679 WILL COLLECT ON SECOND INVOICE diagnostic fee. System number 1 2 ton heatpump.
Upon arrival fault code 84 high pressure lockout. The condenser fan motor would work at lower speed but stop working at higher speed. I replaced condenser fan motor. It is cooling at this time.
Found system off on safety overflow switch. Cleared drain with nitrogen and flushed with Dawn. Mixed dawn with water and flushed system from air Handler to common drain. System is working properly now. Note: customer would like to wait to sign up on service agreement at this time
AC SERVICE REPAIR ON A 3 TON BRYANT HEAT PUMP PACKAGE UNIT. REPLACED BLOWER MOTOR MODULE.
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP PACKAGE UNIT. REPLACED Thermostat
AC SERVICE REPAIR ON A 3 TON PAYNE HEAT PUMP PACKAGE UNIT. REPAIRED BLOWER MOTOR
AC SERVICE ON A 3 TON GOODMAN HEAT PUMP SYSTEM. ORDERED NEW STAT.
ANNUAL SERVICE CONTRACT MAINTENANCE TUNE UP AND CLEANING ON A 5 TON CARRIER INFINITY HEAT PUMP SYSTEM