The technician was knowledgeable, helpful, and on time!
I was very thoroughly satisfied with the service that I received on Sat., the 17th of April. I appreciate the promptness and ability of your company.
It was an annual maintenance. Told me what he did. Cleaned Unit checked levels. Everything good.
Steve makes his company look good. He is meticulous, methodical and careful. We need to clone him.
Even though we didn't purchase our AC unit from Bay Area, they provided us with excellent service. We called at 9:00 am and Steve was at our house around 10:30. He was very knowledgeable and professional. We will be using Bay Area from now on.
Great service was able to salvage my pump so I did not have to buy one.
Really great service
Skilled, knowledgeable staff
WE HAD GREAT SERVICE.THE MAN THAT DID THE WORK WAS AWESOME GOOD JOB
My grandson is new to this area and called Bay Area A/C sight unknown. It was a great experience and so glad he chose this company. Quality of tech and speed of service was just what we wanted. Pricing was very well within reason. Office staff very friendly and informative. Great experience.
Install new filter into a 3-ton Carrier AC system
A/C Service on Carrier 3 ton air conditioner. Performed preventive maintenance.
Floral City Performed annual tune up on Payne ac system.
Ordered x13 blower module for Carrier unit
A/ C Service Carrier 3 ton air conditioner. Added condensate trap to drain line and verified proper draining.
Floral City Performed annual tune up on Payne ac system
Floral City Performed annual tune up on Carrier ac system.
Second opinion for a 2 & a Half Ton Goodman AC
Floral City Performed annual tune up on Carrier ac system
A/ C Service on 4 ton Carrier air conditioner. Replaced supply feed to register boot and resealed boot.
Bay Area professional tune up and maintenance on carrier air conditioning system
Floral City Performed annual tune up on Payne ac unit
A/C Service on 3 ton air conditioner. Performed preventive maintenance.
A/C Service on Carrier 3 ton air conditioner. Cleaned drain pan and drain line and verified proper draining.
Replacing run capacitor on a 3-ton carrier package unit