We needed a new air return vent to cool a bedroom, and it was put in quickly and efficiently, and even though this required cutting into the wall, there was no mess left when it was complete.
Called for service, they showed up within a few hours and quickly fixed the problem.
Jeff was great! Found a weak capacitor and replaced under warranty.He was very organized and the job was well done.
I picked Glen's brain on some issues/questions I had with the system over last several months. He was extremely willing and helpful discussing and answering my questions.
appreciate technician replacing filters
Glen has been my service technician a few times. He is always very informative( he explains why something should be done and the benefit derived from the procedure) and professional. I believe he is an asset to Bay Area A/C.
Dod a quick and cost efficient job..would recommend
Each time I have had the need to contact Bay Area, they have been informative, courteous, and so willing to send the technician to my home in a timely fashion to resolve any issues. Thanks for all you do.
Quote to add 12x12 return grille in secondary bedroom Customer approved
Replaced contactor that was stuck in closed position. Restarted and tested cooling. Customer wants 12x12 return grill cut in secondary bedroom. Cost will be $150 Customer approved.
Replaced thermostat, system operating at this time. No signal, customer will call for payment.
Solder copper lines, evacuate and pressure test. Replaced ID fan motor and cap. Connect all low voltage wiring. Add 2 lbs R410A. System operating and draining at this time.
Service call completed, primary safety switch open on arrival, drain and flush condensation line and advised client to replace air filter regularly, all system vital are good at this
AC SERVICE ON A 3 TON CARRIER HEAT PUMP SYSTEM. EXPLAINED DEFROST CYCLE TO HOMEOWNER.
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 3 TON CARRIER HEAT PUMP SYSTEM.
AC SERVICE REPAIR ON A 3 TON NORDYNE STRAIGHT COOL PACKAGE UNIT. REPAIRED HEAT STRIPS
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 5 TON CARRIER INFINITY HEAT PUMP SYSTEM.
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 3 TON PAYNE HEAT PUMP SYSTEM.
Maintenance checks for our Carrier AC system customers
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. REPLACED CAPACITOR.
AC SERVICE REPAIR ON A 5 TON CARRIER INFINITY HEAT PUMP SYSTEM. REPLACED BLOWER MOTOR AND MODULE.
AC SERVICE REPAIR ON A 5 TON CARRIER INFINITY HEAT PUMP SYSTEM. REPLACED CAPACITOR.
Replace capacitor on condenser for an ICP heat pump air conditioning system in Hernando Beach