Called and had the job done in less than 2 hours!
Quick to respond. Gave prices upfront and did an awesome job. Will call again if needed. Thank you again.
Sales Rep gave us a very fair price. We had 3 estimates from 3 various companies and we felt Bay Area gave us the fairest price. The installers were prompt, courteous and completed the job in a professional and timely manner. We would definitely use them as our service company and would definitely recommend them.
AC was out about 7:00 PM, Bay area AC was at my house by 8:30 and repired the problem
Representative very knowledgeable and helpful.
Jeff is a very nice gentleman. He explained everything that he was doing and why. Very helpful with all my questions and concerns. I will be recording him and your company to all my friends and family. I want to say thank very much for all of y’all help on getting my ac working well again.
Glen did a very thorough job. We were quite pleased with his performance. I would highly recommend Glen. I hope we get him next time.
Robert is a very personable young man. Very knowledgeable and effiencient
Replaced condenser contactor that had open coil. Restarted and tested cooling.
Installed new heat package and wire harness, installed customer supplied thermostat. Tested in both heat and cool
Spoke to customer explained needed repairs.
found connector in unit but up, appears to have been misfires (has a replaced transformer) Viability of heat strip unknown Noted also the thermostat will not "snap in place " correctly Further noted a truss has need cut out; the emergency pan does not encompass the unit; the attic light is all apart ? (electrician required) Insulatuion from the panel was all torn off, had to make repair Office to quote parts
Found existing thermostat not sending signal to start heat cycle. Tennant had new thermost on hand to replace old thermost. Installed new thermost and tested heating and cooling. NOTE System is a straight cool system with only a 5 kilowatt heating element. Size of heating element can not be increased due to wire size to air handler and size of breaker panel without overloading both wire and breaker panel.
De-iced coil, checked evaporator coil, filter and statics. Found charge off, calling for 19.7f superheat, measuring 34f. Adjusted to 20f. Checked td across coul now 21f.
Found primary side of transformer open i side air handler. Replaced transformer and rewired thermostat. Restarted and tested cooling. Send invoice to customer. Has no email.
Perform yearly maintenance checks. System low refrigerant. Added 3 # R410A. System operating at this time.
Found that the system was iced over. Deiced the unit and secured the insulation on the service panel. The filter was really impacted. 15 degree split.
Unable to get a hold of the customer to answer their question.
System low on charge, adjusted charge. Reccomend replacement due to age and condition of system.
Checked over the system to find out why the condenser wasn't coming on. I found a damaged wire within the air handler. Collected the payment for the install. Totalling $5085.00
15 SEER 10 year parts and 1 year labor warranty
Per John, we do not want to get involved with adding freon to pool heaters.
On arrival found that the blower motor wasn't running due to a bad blower module. Replaced the blower module and checked the systems operation.