Very knowledgeable and helpful
Highly recommend to anyone needing ac service
Mark was very professional, called ahead to make sure I was available, and even was able to come earlier than scheduled, which was much appreciated. He took the time to go over the age and capacity of the unit, as I just moved in 2020, and had no idea of its history. When time comes I hope Mark will be able to replace it for me.
I just had a new Carrier A/C unit Installed at my residence. Sal and Cody were very pleasant and courteous. They did a great job!
I’m happy with the company because the quick response and technicians professional service. Thanks Bay Area
Marc was great. Got my system cooling quick.
Great tech, very knowledgable.
Matt Clanton did awesome job diagnosing the problem,finding out if the part was still under warranty to help save me money,and installing my new blower motor.Very happy with the quick service! 😁
Found a tripped float switch. Flushed and tested the drain system. Recommend having annual maintenance.
upon John and I listen to a low loping noise coming from compressor. John is going to talk with manufacturers for remedy to issue.
Service call completed, primary and secondary safety switch open on arrival, drain line clogged, removed water from drain pan and flush condensation line, check system operations, all systems vitals are good at this time
Service call completed, safety switch open on arrival, drain and flush condensation line, check system operations, all systems vitals are good at this time
This is An Estimate to Install A New Carrier 14 seer Heat Pump.
Clear drain and pan and apply drain treatment. System operating and draining at this time.
Checked over the system. The matching 10.year old goodman system is working as designed. The duct system is in poor condition. The life expectancy for an air conditioning system here in Florida is 10-15 years.
Removed the compressor jacket per the customers request. Recommend upgrading to a system that is rated for a lower decibel rating if this normal operation noise is too much to handle. This may offer a lesser operation noise.
Installed the compressor sound blanket.
Goodman pkg unit. No data plate. Repair insulation inside supply box. Perform yearly maintenance checks and cleanings. System operating at this time. Insufficient insulation in attic for unit to maintain temperature at peak temperatures in afternoon.
ID temp at 78, check system operation and found low suction pressure. Added 2 lbs R410A and no rise in pressure. Check static pressure and leak search. Static pressures are high (.78) . No refrigerant leaks detected. Recommend new TXV. Currently producing 66* at supply plenum. 12* TD. Request parts quote asap.
Check system operation. Recommend PM to maximize efficiency. Perform yearly maintenance checks and cleanings. System operating at this time. Disconnect bypassed previously , Recommend a new high voltage run with new disconnect. $415.00.
Found capacitor failed. Replaced capacitor with new 40/5 mfd . System is now working. Old Goodman R22 system. Recommend replacing system. Customer would like 3 ton system. Duct should accommodate. Have Jim H to come give quote.
System cleaning and tune up. System is operating correctly at this time but is showing a lot of corrosion. Taped panels up, screws don't have any metal left to grab.
System cleaning and tune up