Peter Was on time , thorough and honest ! Glad I choose Bay Area Air Conditioner . Had other companies in the past tell me I needed thing's that I knew I didn't need , just to jack up the price . very satisfied!
Cliff was very professional and did a great job providing service to our ac unit
Everyone was so nice, professional, helpful and prompt!
Pete knows what he is doing. Nice to see a familiar face to do my service.
Peter has the technical expertise to fix your HVAC issues. Did not try and sell us something we don’t need.
Was quick and knowledgeable
Called and the next day had more questions. 5 stars with receptionist all the way to manager QUICK response..ALL my questions answered and resolved. This is why they have excellent reviews. I will refer them
Completed tune up
Inspected ductwork in spare bedroom and found no mopd growth in ductwork. Inspected inside of air . System is 16 years old and showing signs of mold growth. Sprayed disinfectant spray in drain pan. Quote for new system.
Call back unit was little low on freon 1/2 lb. Sub cool 9Â° Delta t 17.6Â° before I left.
Found 45/7.5 capacitor bad on compressor side. Installed new capacitor and tested. System now working properly.
Ran complete system tune up. Evaporator and blower clean. Cleaned drain and pan. Flushed system and treated. Checked electrical, motors and capacitor. Amps good. TD at 19 degrees and sub cool at 10.
16 SEER 10 Year parts and 1 year labor warranty
Warranty. Cleaned drain tested system . System now working properly. Note : can not get ecobee stat to hook to wifi. Other than that it's working properly.
Wrapped two sections of metal supply ductwork with new fiberglass duct wrap where existing duct insulation was completely missing. Very important for customer to know that all metal ductwork is rusting and the insulation on supply ductwork is deteriorating very badly and sweating underneath. Recomend replacement of ductwork in future.
unplugged drain line for performance carrier heat pump air conditioning system replaced faulty float switch under warranty in Hudson
AC SERVICE REPAIR ON A 3 TON CARRIER INFINITY GREENSPEED HEAT PUMP SYSTEM. REPAIRED CONTROLLER.
ANNUAL SERVICE CONTRACT MAINTENANCE TUNE UP AND CLEANING ON A 3 TON DIAKIN STRAIGHT COOL SPLIT SYSTEM.
Another tune up done on Carrier Performance heat pump air conditioning system in Hudson
AC SERVICE REPAIR ON A 3 TON CARRIER INFINITY GREENSPEED HEAT PUMP SYSTEM. REPAIRED LOW VOLTAGE.
AC SERVICE REPAIR ON A 5 TON CARRIER GAS FURNACE SYSTEM. REPAIRED GAS PRESSURE SWITCHES.
AC SERVICE ON A 3 TON CARRIER INFINITY HEAT PUMP SYSTEM. ORDERED NEW CONDENSER FAN MOTOR