I had Glen out today to fix my AC since it abruptly stopped working. He came out within a few hours and worked hard to get it to work again. Thank you for your honestly, fair price, and determination to leave me with a working AC without an immediate replacement!
Glenn was very helpful. Great Service
Honest and hard working. Thank you so very much.
Inspected our 12 year old ac, and told us we still had "life" in it. Did not try to sell us anything.. Very pleased with the honest service which is rare in FL. So happy that we decided to get a service contract..
The attendant had to defrost the coil and then fill up the Freon price was reasonable and an excellent job. And showed up within half an hour after calling for service
Very quick response
I found Cliff to be clear, honest and low key. He showed me the reasons for his opinions and provided options.
Extremely pleased with Jeff's work here today, explained everything clearly and gave some great tips to keep my system maintained. Highly recommend
Excellent professional reliable service!
upon arrival the blower was not running. I tried switching speed taps on module but would not start. I quoted evergreen module but homeowner is going to get second opinion.
ODU won't run Found open circuts in stat wires from stat to Attic unit and open cir5 in stat wire from Attic unit to ODU Noted ODU Defrost board has been wired out of control scheme, ALSO, after getting the system to operate it is noted the refrigerant charge is shy of fully charged (indicates a leak probably exists) System dates to 2001, duct system is original (1981) and should able be considered for replacement Quoting new system, without ducting
Perform yearly maintenance checks and cleanings. System operating and draining at this time.
Jeff W. Called customer and walked him through fix.
Found the system low on r22. Recommend having the system replaced as the r22 systems and refrigerant is phased out. Financing options are available.
Handled as recall Sarety float on unit was tripped Found build up of "white algae" in pan adjacent for pan outlet and throught pan basin Vacumed abap and treated with peroxide, note areas of pan next to impossible to clean due to unit design and truss system. Re-primed and observed dripping at outlet Future drain issues will call for a skinny tech and pressure spraying while vacuuming the pan
upon arrival the capacitor was open to fan side and just enough to start compressor. I replaced capacitor CAP455A and tested. The fan motor was overheated. I cooled with water and is now running. It is cooling and draining at this time.
Found condensation dripping from the copper line set. Used cork tape and sealed around the connection at the air handler to stop the drip.
Found drain line and drain pan full of slime and backing up into float switch causing system to shut off. Cleaned and flushed drain line and pan. Added drain tablets and viper pan spray. Restarted and tested drain line and puron pressure. Collected check
System maintenance on straight cool package system.
This is not a service call. Customer needs an Estimate on a new duct system. Completely new duct. Has metal duct system now. Needs flex system installed. Got pictures of duct. System was moved from attic to garage. Need Jim to come give a quote on a new duct system and possibly new A/C system separately. Note: very tight attic More involved on estimate than I usually give. Great Lead for Jim and customer would like to get estimate on new complete system Duct and Air conditioning. Talked with him about financing system and he likes that idea. That way he can get it all done at one time.
Cap was reading at 1.0 on fan and 30 on herm fan was not coming on put new cap in rla is 5.1 and fla is 0.7 unit is running ok. Very old unit
System was iced over on Sunday. Restarted and tested cooling. Found extremely blocked return air filter restricting airflow to airhandler. Removed filter and tested cooling. System is working but has a mild restriction in the freon circuit. It has more that one filter drier installed and suspect tx valve is restricted. However do not recommend replacement of tx valve or any major repairs on this system due to age of system. Over 16 years old. Recommend system replacement soon or before next summer.
Drain line was clear upon arrival. Found system low on 410a. Leak searched system. Only leak found today was on suction line service port that was missing cap. Replaced cap and added two pound s of 410a to syste,
Custmer signed up on silver contract today . Did maintenance for that contract today.