He was thorough and explained everything to me !
Great experience, very helpful and friendly. Explained each step that was needed to get it working as well as maintenance needed in the future. Thank you so much!
A wonderful experience. Very professional.
Bay Area Air Conditioning is the only company I'll ever use for service or a new installation.
Highly Recommend,quality service! I wont call or deal with another company
Honest , on time if not early , great workmanship ,
8" run from plynum to 6" run to bed room 25' long
Checked over the system and didn't find any issues. What the customer was experiencing was the system going through defrost.
Completed the maintenance inspection. Found the system low on 410a. Added 4lbs and found a leak at the outdoor TXV. Note: The TXV is also closing down during the heating cycle which lead to the compressor over heating.
Upon arrival the system would not start. Strsight cool with electric heat. I turned to heat but had no low voltage. I looked down and noticed float switch pipe was tilted up. I removed float and found it stuck in the up position. I removed all the spider webbs and freed switch and system is now running.
Airflow to front bedroom very low. Duct is installed per sizes on drawing. Room has 3 exterior walls. 12" duct to distribution box approximattly 25ft, 6" flex from distribution box to bedroom is approximattly another 25ft and connects to existing 6" metal duct to bedroom. Last 8ft is inaccessible. See picture
Checked over the system and found no issues. The system turned on heating and cooling. Explained the thermostat's operation and answered all questions.
System was observed operational in lo & hi stages Verified different pressure operation values at 3 different startups in hi speed & outdoor unit turning off for unknown reason (no faults recorded), much lower pressures were also observed indicating low charge. Suspect either outdoor board, controller, or stat wire cause miss communications Recommend use of Aux Heat for temporary Any labor charge is bearing on closing / not closing sale buy Jim H. (120$)
Checked package system. 2007 System is a 2 ton straight cool system with a 5 kilowatt heating element. Not a heatpump Heating element is working but thermostat must be set to EM HEAT to operate heat. If thermost is set to heat the cooling will turn on. Filter size 18x24x1 Whenever system is ever replaced main electrical service will need to be upgraded unless the county will grandfather in existing electrical service.
service call completed, system had a blown fuse upon arrival, replace defective component, unit up and running, noticed burning spots on the control board, inspect wiring and cover small sections near the 24 v transformer, disconnect u.v system since it was not operating upon arrival, recommended to replace u.v system and connect with a separate transformer , at this time no parts need be ordered
Tried calling and left a message for customer to call me back or shop
Replaced electric heat sequencer to get heating working in some forem. System has two elements and one is no longer repairable. System is only able to operate on 50% heating capacity. Left quotes for new system. System is very old and in poor condition.
Found system turning on and off continuously. Checked 24 volt wires and found no breaks. Faulty stat is what I found. Note I installed a temporary stat to insure customer that this was the problem . After installing new stat I discovered what caused the problem with the old stat. The disconnect was melting down.
14 SEER 10-YEAR PARTS AND 1-YEAR LABOR WARRANTY
upon arrival the heat strip was not coming on. I found loose wire and terminal burnt. I cut bad end off wire terminal and it is heating at this time.
upon arrival nothing was responding from stat. I open cabinet and found loose float switch wire. I went through parameters on stat to make sure it was set up for straight cool. I tested in heat and cool a couple of times each to make sure it would work.