The price seemed high.
On time, pleasant technician, cost was fair.
Excellent service at a fair price. Bill came to our home and corrected major mistakes our previous AC company made. I appreciated that he took the time to explain everything. Thanks again Bill!
Very much appreciated that the service technician got to us so we were able to have a comfortable nights sleep
Jeff was amazing. He was professional and worked his tail off. We really appreciate the service he gave us.
System is beyond repair. Thawing system out was about all that could be done and putting in filters that have no restriction. Recommend replacing system. System was double filtered. Filter at A/H was plugged. This caused System to freeze up. R22 Charges were good at 75/225
Ran system check and found no problems at this time. System was holding 72Â° when I got here. So I went ahead and checked anyway. System working within factory specifications. While I was checking system i ran shop vacuum on drain as a courtesy.
System isca complete block of ice. Straight cool. Nothing i can do to help tonight. Reschedule for tomorrow to diagnose problem or problems. Did not charge because I couldn't do anything at this time
Ran complete system tune up. Found no problems. System working within factory specifications. Cleaned and flushed drain and coils.
Annual ac tuneup and cleaning. I checked refrigerant pressures and static pressure. I checked all amp draws. I checked temp splits. I checked capacitor and contactor. I waxed outdoor unit and cleaned both coils. I flushed drainline and added drainsolve. Then I flushed drainline multiple times and removed slime build up. I did not find any issues at this time.
remove old and replace. Seal in around ceiling and tie duct runs back in. 2 people 1 hour each
Ran complete system tune up. Cleaned coils and drain. Flushed and treated. System working within factory specifications. Note: Filter needs changed. Customer is going to purchase and replace.
Clear drain and pan. Recommend replacing system as this system is not installed to code. Delta temp is low. System operating and draining at this time.
Perform yearly maintenance checks and cleanings. System operating and draining at this time.
Quote on new system
Found capacitor completely dead . Need to replace. Replaced capacitor and completed system check. System working at this time.
Tune up complete