Show up on time ( was even early ) and explained what the unit was doing. I completely satisfied with the explanation and service. Thanks for your promptness
David was very thorough, and took a great deal of time checking. Thank you.
He has been here before and we asked again for him. He is knowledgeable and worked hard. I would recommend him to my neighbors.
He did a wonderful job and will be back with a new fan. I like him a lot!!!
Bay Area researched my record and found that my a/c was still under warranty. I may never have known.
Jeff realized the problem immediately and went right to work fixing the problem (broken pipe). He is friendly, honest and I will definitely recommend him to my family, friends and neighbors...👍🙂
Ran complete system tune up. Cleaned, flushed and treated pan and drain. Tested charges, electric and static. System working properly at this time.
Annual ac tuneup and cleaning. Straight cool system with electric heat. I checked all operations but did not keep ac on long do to cold morning.i checked heat strips and amp draws. I checked capacitors and contacts. I waxed outdoor unit and cleaned both coils. I did not find any issues at this time.
Perform yearly maintenance checks. Added 3 lbs R410A to achieve desired subcool. System operating at this time. Warranty. Customer declined to pay, request office to arrange payment.
System was going into defrost customer felt cooler coming out during defrost mode has 5 kW heat strip explain defrost mode customer let us know if there's any other issues
Went over tstat with customer drawed a diagram for tstat and dampered off run to her master bathroom
Customer didn't know how to work tstat went over it with them! system is running good
controller has no temporary faults Last 10 shows 255 hi static 1 hi stage fault 1 lo stage fault Through checkout proved ODU capacitor ok: controller measured static correct (1.06 TSP) and refrigerant values were within parameters Cause of prior malfunctions undeterminable at present
System wasn't communicating with outside. Reset breakers & tstat. Unit came on no further problems.
Found bad tstat. Customer had new to install installed new one system is up and running. Delta t 16Â°
Blown fuse bad defrost board
Found w- wire hooked to y-1 Ã— w2 needed to be on w1 moved wire tested system and reprogrammed configuration mode to proper settings. System now working properly.
Customer could not get financing - cancelled
completed duct work on 11/25/20 - #96228131
All labor and material included
Installed turning vains in both supply and return . Warranty. Customer is hearing hot gas line at night during very long run cycles. Used 5 turning vains