Jeff did a wonderful job. Very professional . We Appreciate his service an asset to your company.
right price, Jeff Myers very professional.
He did a thorough Service, Thank Jeff
Complicated issue, service tech was knowledgeable and a good person.
Pete is a credit to your company. Has good PR. I always ask for him to come out on the call. Knows what he is doing.
I had an annual cleaning and tune up performed this morning. My technician’s name was Jeff and he was great! He was thorough, knowledgeable, and polite. The office is always very friendly when I call to schedule appointments on either of my homes and they are very accommodating to my needs as well as the needs of my tenants. They are also very fairly priced so that servicing doesn’t necessarily need to break the bank. I have found this company to be honest which is hard to come by and goes a long way with me!
I would recommend Jeff Woods to all Bay area customers.
Taped insulation on suction line were tripping water in attic customer wants plenum to be cleaned up and resurfaced after she has ceiling in garage done for her $100 to do that she'll call the office when she's ready
Fallow up on call. Found txv valve bulb not attached to suction line. System under charged by 2 lbs . Checked for leak and found none. Calls for 14 degree sub cool. Got it to 14 degrees. No diagnostic because we were here two days ago
Couldn't check refrigerate cause of key style locking caps, cleaned drainline
14 SEER 10 year parts and 1 year labor warranty
Tune up completed, drain and flush condensation line, advised clients to replace air filter regularly, clean condenser coil and evap coil, check refrigerant pressure and electrical components, all system vital are good at this time
Service call completed, low voltage problem upon arrival, during inspection found low voltage connected to the high voltage on the contactor and capacitor, replace fuse and condemned thermostat, replace defective component, tested equipment, all system vital are good at this time
Installed a temporary system, 410a 3 ton , new system installation date on the first week of September, client provided with a check for $500.00 the spike unit , the check it will on hold until the new system is installed , check number 1628
Changed out modular on i.d blower motor. I installed a 3/4 hp ecm 3.0 modular, needs to be a 1/2 hp 120/240 ecm 3.0. left blower in box at house. Also found that defrost control board o.d unit went bad put bleck leg from fan to defrost board to contactor.
Found compressor was over heated ran water over compressor till cool fired it up. Low on freon around 1 lb.
System down and out , compressor lock on thermal overload and lRA , recommended system replacement, client will call Monday with the decision of system replacement, client look into the financial options
Could not find a problem with system. Nice and quiet of course. Checked charges amp draw , electrical and for a critter that may have got caught in fan blade. System is working properly and no noise at this time. Warranty
Service call completed, secondary drain pan switch open on arrival, removed water from drain pan , drained and flushed primary drain line , heavy slimes and debris found in condensation line, strongly recommended to replace air filter regularly, system is cooling at this time
Service call completed, system wasn't cooling properly, during inspection found dual capacitor not operating to normal specs, refrigerant levels was slightly lower, advised clients system condition, replace dual capacitor and add 1.25 lbs of 410a, clean condenser coil and flush condensation line, retested equipment, all system vital are good at this, client sign up for silver maintenance contract, scheduled tune up in 6 month
ANNUAL AC MAINTENANCE TUNEUP AND CLEANING ON 3 TON CARRIER INFINITY GREENSPEED HEAT PUMP SYSTEM.
Annual service contract tuneup and cleaning on a 5 ton CARRIER infinity heat PUMP system.