The service was great, Robert knew what he was doing and what he was talking about. He had it up and running in no time.
Our second year with your company's service and are very satisfied thank you Joan and Richard Thompson
The tech was friendly, knowledge and diagnosed the problem (leak). Repaired AC in under 2 hours.
Really happy with the service. Glen was professional and quick. Price was very fair. Glad to have the unit all tuned up and ready to go!
I first used Bay Area Air Conditioning 3 years ago, to resolve an a/c issue. Because of the excellent service performed then I had no hesitation in reaching out to them to service my a/c again. I called at 8:00 am and a technician was at my house by 12:30 pm. The technician was diligent, knowledgeable professional and patient with all my questions. The service call was for routine maintenance but he identified and repaired a few air leaks along with cleaning a clogged drain line. I would definitely recommend this company to family and friends.
Very thorough annual maintenance check-up. Helpful discussion on outlook/longevity for a 17-year old A/C unit, and advantages of replacing with 1 unit/zoning feature vs. 2 features. Really appreciated being offered "first appointment of the day" to reduce time away from work.
AC SERVICE REPAIR ON A 2 TON TRANE STRAIGHT COOL SPLIT SYSTEM ADJUSTED FLOAT SWITCH.
AC SERVICE REPAIR ON A 5 TON BRYANT HEAT PUMP SYSTEM. Removed old condenser and installed temp unit until new system can be installed.
AC SERVICE, 2 system clean and check for a new customer last year
Carrier system maintenance
AC SERVICE REPAIR ON A NORDYNE HEAT PUMP SYSTEM.
Tune up on carrier hvac heat pump air conditioning system in tampa
Carrier system maintenance two systems
CARRIER SYSTEM MAINTENANCE
Replacement of zone control
Did tune-up on Carrier AC system
AC SERVICE REPAIR ON A BRYANT HEAT PUMP PACKAGE UNIT. REPAIRED BREAKER.
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. REPLACED BLOWER MOTOR MODULE.
Did tune-up on Carrier Furnace AC system
Annual ac maintenance tune up and cleaning on a 4 ton Carrier Infinity Greenspeed heat pump system.