Bay Area responded within several hours on a Saturday and repaired our inoperative air conditioning system. In addition to replacing our thermostat, he checked the operation of the system and ensured our overflow tubing was clear.
Always professional and knowledgeable and honest in every way. Bay Area Air is my A/C company.
Jeff was AWESOME! Best AC house call ever had. Jeff showed up on time and gave us an honest evaluation and quote. We will continue to do business with Bay Area. Ask for Jeff!
These guys came out and were extremely courteous, experienced, patient and completed the work professinally. I highly recommend them to everyone and will continue to use them for all my A/C services.
Had a cracked pipe after a service call resulting in a leak. Called the office and they had someone come out immediately at no charge.
Very dependable and customer friendly company. Fair pricing too
Very professional, polite, knowledgeable, and fast.
The technicians are consistently knowledgeable and help fix whatever the problem is. Such an incredibly honest company too.
Found a tripped float switch. Flushed, treated, and tested the drain line. 18 degree temperature split.
Returned to find the thermostat to be flashing on and off. Replaced the thermostat. Left the out stat with the customer just in case the problem continues.
The thermostat wasn't seated on the wall 100% not allowing a good connection which is intermittently removing power from the thermostat or remove some wires tighten some connections insured thermostat is seated correctly
Had office attempt to verify responsibility of services (tenant-landlord) Owner said no go, he has ac service scheduled for Friday with others
system frozen solid, will need free of ice to further diognose
Found insulation around the flex duct which was causing condensate around the supply duct box. I also found that the dehumidifier's drain system isn't insulated. Will need to return with another tech and fix the pitch of the drain and insulate it.
System #1, 17 yr old trade 5 ton System was frozen , solid ice thru & thru in evaporator Determined thermostat failed to operate indoor Quoted & replaced stat, Travis to restart system on Monday, and hopefully all will be OK Additional trips are chargeable
Payment on invoice138904972 Systen marked #1 Routine maintenance Noted all system functions and operations were normal and within parameters See invoice 138904972 for NOTES
Equipment marked #2 Routine maintenance Functions and operations were normal with exception to the emer pan was filling up with water Vacumed both drains from indoor location and treated both units with Viper drain pan treatment and both drains with Drain Solve Drain outlets could not be located ? If need be will require 2 men and additional charges
test & checked system, all operations normal and within parameters Suspect prior complaint arose due to system being off for 2 days, also glued loose fitting on drain safety
testing shows that at 58Â° to 59Â° the existing OST measured 1.3ohm, the new sensor at same temp measured15.6ohm Replaced OST thermistor
No one's answering the door for 25 minutes. Checked on the system to find a tripped float switch. Recommend having the drain line serviced.
checkout system, functions and operations were normal No heaters components operating Cause for hi electric at present are not related to AC system Left estimate for new systen based on existing age (25yrs old) Office to mail all copies
Testing proved system fully operational with normal values, however suction line temp sensor out of range is persistant, ordering external sensor
Completed the maintenance inspection. No recommendations at this time.