The technician was courteous and on time.
Thus far, I have been very satisfied with Bay Area A.C. Please send me this form seven months from now when I will be able to accurately assess the latest work done. Thanks.
I called Bay Area for the first time, to do routine maintenance on my HVAC yesterday. Service tech Glen was very professional and courteous.... Respectful of my home and his work was clean. He explained what he had done and found, answered any questions I had and provided helpful suggestions for better efficiency. He also took the time to give me some information on the purchase of a new unit in the future. I felt very good about the service, quality of the work and Glen's knowledge of the product. I will be sure to contact Bay Area for all future HVAC needs! Thank you again Glen!
Glen was at our door an hour after a call late on a Saturday afternoon that the A/C had quit cooling. He had it back up and working in 30 minutes and leak tested it. He went out of his way to show us how to get the maximum out of our system until we returned from vacation. Excellent service.
Hard to judge with only one estimate
Jeff explained things in a way I understood, was efficient and pleasant.
Please have someone call me at 727-741-1113. My rating for the technician is excellent. The Local office is poor.
10 year parts and 1 year labor warranty
Yearly tune up completed, drain and flush condensation line advised clients to replace air filter regularly, clean condenser coil and evap coil, check refrigerant pressure and electrical, system is 10 years old, moderate rust on evaporator coil, system draws higher energy consumption, advised clients system condition, system is cooling and working at this time
14.5 SEER 10 parts and 1 year labor warranty
AC SERVICE REPAIR ON 4 TON CARRIER INFINITY GREENSPEED HEAT PUMP SYSTEM. REPLACED FLOAT SWITCH.
Found drain backing up and shutting down system. Cleaned, flushed and treated drain. Tested and waited to make sure of good flow. System draining properly now
Corrected charge on newer system installed by other co.
Verified system performance. Checked refrigerant levels and amperage draws from the compressor and fan motors. Everything was good. Cleared the condensate drain line and added drain treatment . Cleaned the indoor and outdoor coils and waxed the outdoor unit. Customer would like to sign up for a 1 year contract and get an estimate for a dual head mini split installation . Filter model # GAPCCCAR2420
Ran complete system tune up and found no problems. System working properly, amps charges electrical good. Cleaned drain and system
Estimate for new system
Repairs to a Carrier attic unit, electrical component
Maintenance checks for our Carrier AC system customers
AC SERVICE REPAIR ON A 5 TON GOODMAN HEAT PUMP SYSTEM. CLEARED CONDENSATION DRAIN LINE.
AC SERVICE REPAIR ON A 3.5 TON TEMP STAR HEAT PUMP SYSTEM. CLEARED CONDENSATION DRAIN LINE.
AC SERVICE INSTALLED A NEW ENERGY SAVING 2 TON CARRIER STRAIGHT COOL SPLIT SYSTEM.
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. ADJUSTED REFRIGERANT CHARGE.