Great Job on getting there on time
Jeff is super awesome and is great to work with. I havw referred you and him to all my friends
So glad we could get service right away and Jeff is always so kind and explains everything very
The service and the technician were excellent. He came to the house on the scheduled time and provided preventative maintenance. In addition to the maintenance, he identified a part in the AC unit that was starting to fail. He quickly replaced the part and I could not be happier.
Called company to have my ac units checked and cleaned. got job scheduled within 3 days. Technician arrived on time, was very pleasant and answered all my questions.
Jeff show up early PM as scheduled. Jeff went about taking care of my problems and very satisfactory repaired the over flow and drained the tray below the air conditioner. I would highly recommend Bay Area to my neighbors.
I will say that soon as my Serve with Superior runs out we would like to do the Service Contract with you. Thank you and let Jeff know we are very satisfied with him.
From the moment I called to schedule an appt through to job performance, your customer service was amazing. Professional, knowledgeable, would use again and refer without a doubt.
i have been with Bay area air conditioning as a customer for 20 years. i called the other morning at 4.30 am to their answering service with an emergency. they had a technician to me by 10 am the same day. The technician was first class .
The technician was someone familiar to us and with our cooling/heating units because he had installed and maintained them previously. I felt comfortable having him work in our home and servicing the units inside and out.
Clear drain and pan. Dripping from evaporator coil due to excessive pet hair buildup. Recommend replacing system with new Carrier AC system, unit is 15 yrs old and R22. A pull and clean service is 474$ with no guarentee that coils won't develop a leak. Currently refrigerant pressures are good, 75/ 220. Picture attached of coil.
Found the system had the breaker off and a dead frog behind the AOC board. Reset the system to find error code 48. Loss comm. With inverter. Recommend replacing the inverter and control board. Will place the order today.
routine maintenance Functions and operations were normal and within parameters
Perform yearly maintenance checks and cleanings. Replaced AH float switch. System operating at this time. Unit #2 , closet attic
Perform yearly maintenance checks and cleanings. System operating at this time. System #1, garage attic
all 3 air handlers in attic need to reschedule for a first call
Controller has 255 events of blower motor comm fault (255 is max can be recorded) Quoted motor at $1526.00 & left system quote Per customer, replaced motor and tested Customer to request new UV Bulb with next maintenance or pay for return trip
Perform yearly maintenance checks and cleanings. System operating at this time
Annual ac tuneup and cleaning. I checked refrigerant pressures and static pressure. I checked temp splits. I amp draws. I cleaned condenser could not wax do to light rain. I cleaned both coils and flushed drainline multiple times. I did not find any issues at this time.
Annual maintenance Complete system check & clean Replaced filter Noted UV bulbs not functioning, blackened on both ends, suspect bulb failure New bulb would be 110.00 on next visit for a maintenance or return trip fee if in-between
Service call completed, upon arrival check electrical components, found blower run capacitor open, replaced defective component and check refrigerant pressure, system check out low of refrigerant, charge 3 lbs of refrigerant, performed a quick leak search and no leaks found at the moment, advised client system condition, unit is 9 years old, there is some areas impacted with rust , systems aren't in warranty , send a free quote for system replacement in case client want to upgrade for a better efficiency system financing options are available , both systems are operating at this time
Found that the disconnect was pulled from the air handler. On the earlier visit today they must of forgotten to added the disconnect. Serviced the drain line and checked the systems operation.
old breakers match new system none needed
Ran complete system tune up. Found a short at A/H and fixed it. Found no other problems. Static was at max for duct system. Cleaned drain and coils. Treated coils and drain. System Orting within specifications.