Got the job done!!!!
Wonderful a 10 out of 10
Checked swamp cooler, found water pump locked up with debris. Cleared, still did not run, cleaned out pan, installed new pump. A/C repair in Brookfield Co
Shower valve was stuck closed and would not open up. Brass stem was broken inside valve body. Ended up replacing entire shower valve and shower head.
Jordan on 6-29-21 removed old outlet and installed 30 amp fused disconnect for water heater
Water heater failed due to expansion tank not being supported and something to do with the wiring. I strapped the tank and inspected the wiring. I noticed the hot wire had a little bit of wire showing under the wire nut. I trimmed wire down so the wire nut was completely covering wire. There was no inspection report left and tenant was told she could look it up online. I had no access to the report and fixed what I saw wrong to the best of my knowledge. No charge for warranty issue.
I Paul arrived at the above address because the customer said the out door unit was not running. I check the condenser was locked out on low pressure. I check the switch and it was closed so I restarted the unit turning the power off inside at the furnace then turning it back on to clear the fault. I had hooked up my probes to check the pressure and when it came back on the pressure was high 410a highside 406psi subcooling 3 lowside 167psi superheat 0. I recommend that the customer have her condenser coil because they were plugged with Cottonwood. She OK to work to be done so I remove the side panels and clean the coils then put the panels back on and checked pressures again. The indoor coil is a EEV valve. I took pictures of the pressure after I was done all is okay at this. The customer paid 858.00 with a visa credit card there is no warranty on work done today because there where no parts replaced.
Boiler repair. No heat
Boulder repair. No heat
Water leak in ceiling below bathroom in Broomfield.
Furnace repair in Broomfield
Boiler repair in Broomfield
Kitchen sink drainage installation in Littleton.
Replacing control board and high limit.
Disposal install, Broomfield.