Jim Womack has done work for us before and he continues to provide great service.
Like other Bell employees who have worked in my home over the decades, Jordan was knowledgeable and pleasant to deal with. Bell plumbers, electricians and other technicians inspire confidence.
Matthew Holbrook was the repair person all of us dream of but rarely get. He was polite, professional,informative,respectful and most importantly took care of the issue .
Our system quit working because the compressor would not turn on. I knew the breakers were on and not the issue. It turns out a small but was fried between the contacts that fire up the compressor. This kept the compressor from turning on and caused the air conditioning to only blow hot air. The fix was extremely quick and excellent.
One of our main sewer drains began to back up this morning. I called Bell right away and Jazper was here within an hour. Very friendly and thorough. Took care of it and all was back to normal fast! Thanks!
Jasper was professional, friendly and explained the job thoroughly. Will definitely call Bell again in the future.
Travis went above and beyond explaining everything as our job was a little complicated! Great personality too!
Diudonne was wonderful, did a thorough job and explained things along the way.
Cut out leaking bleeder 90 Added new valve with bleeder
Replace T&P on water heater.
Trip charge, clear and reset garbage disposal. Leak tested. Functioning properly. Standard service. No warranty. Paid $324.00 by check #2003.
Denver Ac issues
Membership, reroute plumbing for vanity, replace hose-bib, add ice maker 1/4" line, remove and replace master lavatory, add prv and new house main valve. New value maintenance members. 2 parts and labor warranty. Paid $3103.05 by card
Aurora - Ac no cool
Observed water in off position. Turned water on and observed low pressure before service. Customer requested main water and isolation valve shutoffs replaced. Rebuilt and tested manifold located in floor. Left new valve in the off position. Please note curb stop key is required. Meter pit does not have a shutoff.
1. Furnish and install new disposer. 3 year in-home warranty. No warranty on existing continuous waste piping. 2. Repair Moen shower valve at basement bath. Two year labor and material warranty. Paid by card.
Chris Rosales and Derek came out to replace compressor due to short to grow on old unit. Place old 420 A in a tank and flushed the line set with acid flush and purged with nitrogen. Added line dryer to both sides of refrigerant and test for leaks, no leak and unit vacuumed down to below 500 microns. Test unit, added 14 0z of 410A to achieve subcool of 12. uNit is cooling at this time, will need to come back in one week to take out filter dryer and contaminated refrigerant.
AC Repair - Denver
Diagnosed capacitor And replaced capacitor with dual run capacitor.
50 gal electric water heater and hose bib replacement
Complementary estimate for plumbing repairs
Aurora - Ac
Electrical service-Repair two outlets