Was careful and good at problem solving
Austin was our service technician for an electrical breaker that would not reset. First he determined that it effected 2 bedrooms in the basement. He replaced the breaker, but that did not solve the problem. He then had to begin removing the wall plugs and switches until he found the issue -- a ground wire in one switch was causing the breaker to kick out. He replaced our original breaker so he did not charge me for that, returned all the furniture to its place, and completed everything in one hour. Thank you Austin!
Aaron was awesome. Right on time and very knowledgeable.
Jay was excellent in explaining what the issue was.
Travis was pleasant, helpful, timely, efficient
Travis was friendly knowledgeable and efficient. Great results for a reasonable price!
Conscientious, professional but also personable
Quickly and efficiently performed the removal of the gas on off valve.
Excellent service, leaves the work area clean, willing to answer lots of questions and reviews critical info to make sure we understand.
Above and beyond expectations and took my coupon!
First time with using Bell, they were able to make it out the same day and fixed the issue
Lake call this evening a customer had I believe a freeze and break on the waterline going to the back yard hose bib after discussing what needs to be done to make the repair Mr.Cerise and thought it to be a good idea to just cap the line for now and deal with it in the spring being we donâ€™t know whatâ€™s behind the all it was located behind the master bedroom fireplace .cap on water on no leaks
Aqua therm air handler
Customers PRV was not working high water pressure 130psi no matter The adjustments. Was able to replace PRV in basement.
Cabled & Cleared Shower Drain Line. Paid in full with a card. Tech: Tomas.
Cabled & Cleared Main Line. Paid in full with a card. Tech: Tomas.
Home owners need an adjustment in water pressure. I adjusted to 70psi per customer request. The PRV looked to be in good shape no water hammer sounds during the visit.
Customer had prv that some else installed incorrectly. Had a beveled edge on one side and the pipe flange was flat. Replaced prv with new one with correct flange assembly and gasket.
Hole house inspection House was very good except for some push pull emergency stops
Electrical service for troubleshooting
Cap water line in place of expansion tank replacement due to 14 year old tank and open water system. Enrolled in the Value Maintenance Plan for one year. Two year labor and material warranty on supplied material. Paid by card. Pressure reading taken at water heater drain valve is 100 psi, therefore water pressure reducing valve is not working at 75 psi. maximum. (25 psi - 75 psi range). Provided task options for water pressure reducing valve installation with or without additional shut off valves. Provided task for water heater replacement.
Sump pump replacement
Did full inspection on the condo and plumbing looks good apart from the bathroom stop valves they are a 2 in 1 design with supply lines known to fail plastic. Advised customer 8 replacements.
Arrived on site, client water heater leaking from entire unit. Gave options for replacement, with venting upgrade. Client authorized work, declined vent upgrade right now. Returning tomorrow 1/14/2022 to install water heater. 1/14/2022 Returned to install new water heater. Shut water down to home and drained system. Cut out and removed old valves and water heater. Installed new shut off valves on hot and cold water lines. Installed new Bradford White 50 gallon water heater. Thermal expansion tank tank after valve supported to heater. Installed new gas shut off valve, flex line, and drip leg at gas control valve. Installed water heater pan pointed toward floor drain. Leak alert alarm set in pan. Reconnected to existing 3â€ flue vent. *advised client the venting may fail inspection. If it does fail inspection for flue venting issues, client understands it will be a chargeable return trip to upgrade flue venting/common wye. Client has estimate to upgrade venting if necessary* Turn
Nut was loose on prv. Tightened nut and leak stopped. Schedule an opportunity for HVAC to come out and do inspection on customers furnace today January 14th between 2and 4 pm. Payed with check.