Toilet auger Northglenn
Electrical service- change out existing smoke and carbon detectors
Left message and callback number for Marjorie for approval for this task,. Waited 15 minutes for a return call. Will reschedule after approval. Left message and callback number for Marjorie for approval. Waited 15 minutes and did not receive a call back. Will reschedule after receiving approval. Return trip Thursday, August 19: pull existing toilet from hall bathroom and remove from premises. Found a stainless steel repair ring secured to the floor slightly offset from center line of drain and held down with rusted screws and washers. Removed this ring and installed a new centered and secured closet flange. Furnish and install Toto Comfort Height toilet. Five-year labor and material warranty. Office has payment information via prior Telephone scheduling. Please mail a hard copy of the invoice to Marjorie and Gene.
Diagnosed blower motor needs replaced. Ordered through carrier. Has a 2 yr part and labor. Re diagnosed and found control board failed as well as blower motor. Control board not charged for on this ticket.
Open winding on compressor. 20 year old system. Recommend a free estimate on a new system.
Chris McQuistion came out due to no cool. Performed diagnostic. Found system to be flat. Found that the indoor coil was leaking refrigerant. System is only 6 yrs old. Gave customer option of replacing indoor coil. Got permission to perform work. Had to order coil and return next Wednesday to replace. For the time being gave customer 6 lb of r410@ refrigerant to keep cool until we can come back and replace indoor coil. Scheduled to come back Wednesday the 23rd of June. Ordered coil to be delivered to shop. Chris McQuistion came back with correct components. Started by shutting off system. Recovered refrigerant into condenser. Cut out old indoor coil. Replaced with brand new indoor coil. Replaced all pvc drain lines from indoor coil. Brazed in line set. Wrapped up copper piping with insulation and installing TVs on outside suction line correctly. Went outside and nitrogen tested 300 psi at 15 minutes. Held nitrogen test. Next began vacuuming down system to 500 microns. Held decay test fo
Water heater repair