Benson's and its staff have always been super.
Performed a summer time tune up on a trane heat pump in Tallahassee.
Performed a summer time tune up on a Lennox heat pump in Tallahassee. Replaced a 20x20x4 honey well filter.
Performed a summer time tune up on a heil heat pump in Tallahassee. Evaporator coil is in poor condition, recommend replacing it. Will email estimate for a new one.
Preformed a one time tune-up on one heat pump system. I checked the system in heat mode, emheat mode and cool mode. The 20x25x1 filters are good. I flushed the drain line out with a shop vac. The blower motor and the capacitor are good. The condenser fan motor, the compressor and the dual run capacitor was operating within factory specs. I sprayed out the condenser coil with the water hose. The system is operating properly at this time. To note the evaporator coil does have a lot of rust on it but it is still working. I offered to have a Comfort consultant schedule come out for a free estimate on a new system. The system is running good but the phasing out of the R-22 refrigerant and the system is 18 years old. The customer declined but said he will think about it.
Found that the downstairs thermostat was not working. Looks like it was shorted out by roaches. I recommended and installed a Honeywell T6 thermostat 2Heat - 1 cool. The system is operating properly at this time. The new thermostat comes with a one year warranty though.
I performed a summer time tune up on two air conditioners in Tallahassee. I would strongly recommend replacing the capacitors on both outside units. They are getting weaker and this can cause the compressor to run harder.
I performed a summer time tuneup on a Lennox heat pump in Tallahassee. Changed 20x25 Honeywell filter.
I preformed a summer time tuneup on an Amana system in Tallahassee.
Today we performed a tune up on your two Goodman heat pump units. We also replaced the two 201 air filters. The upstairs unit is not cooling properly and we will send out a service tech to diagnose the issue. The downstairs unit is working properly at this time. Thanks you for your business. Tallahassee FL
Performed a summer time tune up on a ptac system in Tallahassee.
Performed a summer tune up on a American standard heat pump in Tallahassee. The system is working properly at this time.
Performed a summer tune up on a carrier heat pump in Tallahassee. The system is working properly at this time. Sent an estimate via email for a surge protector and a primary drain safety switch.
I performed a summer time tuneup on two American Standard heat pumps in Tallahassee.
Performed a summer time tune up on a Goodman heat pump in Crawfordville.
Preformed a cleaning on the Gree mini-split head in bonus room. Cleaned and sanitized indoor blower and coil. Tested system and it is working properly at this time. Cost is $140, applied credit of $92.50, collected remaining balance of $47.50. Job complete.