No respect. Estimates do not match. Unprepared. Wrong furnace, so delays. No ladder, delays. Cannot respond to their texts or their e-mails. Don't care if you freeze while they work. Furnace removed w/o a new furnace to install. 24 hours without heat. Awful! No discount for inconveniences. Require full payment before job completion. Very crooked vent out of roof.
BHH does an excellent job of giving you an appointment at your convenience. The pre-appointment follow up is excellent and the technicians are very courteous and really care about your satisfaction. I highly recommend Black-Haak.
Brad and Trainee arrived perfectly on time. I left them to do the inspection and cleaning. I have great faith that all went well. Black-Haak has always looked after me very well. Thank you!
Technician "Craig" was great. Work was done efficiently and explanation was on target.
Kody was very personal and got the job done quick!
Preformed furnace C+T. Things were fairly dirty due to customer finishing the basement. Custmer mentioned they had some issues with humidity levels in the house during the winter months.
This is a quote to install the heater for you. I was working on the pricing for this and 800 is going to be my best price on this. I wouldn't be able to go any less. Please let me know if you have any questions! 4-20-18 Installed owner supplied unit heater. Used owner supplied b-vent except 1-4â€ storm collar. Gas line and thermostat installed.
Friends and family furnace clean and tune. General heat exchanger ware. Cleaned sparker, burners, and flame sensor. Checked ventor motor and blower motor. Checked gas pressures and combustion. Checked for CO in exhaust and airstream, both ok. System operating normal at this time office to call on Monday to ask about ac clean and tune. Quoted ac clean and tune and electrostatic filter price. .
4-20-18 brad and devin ran gas line to stove. Checked for leaks and made sure all gas appliances were light.
I upgraded the filter with an Aprilaire 213 upgrade kit and filter. I also fixed the venting leak that was noticed during the furnace cleaning. Everything is working properly. Miscellaneous task is for the venting repair.
Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. Furnace is running normally at this time. Performed indoor coil inspection. Checked for refrigerant leaks. Didnâ€™t find a leak at this time.
We removed the old furnace and installed a new unit. Tie into existing duct, gas line, venting and electric. Ran new drain.
4-19-18. Brad and Devin. Fixed venting leak at 90 going down to furnace. Ran furnace through a cycle to make sure there were no more leaks.
Furnace clean and tune. Found heat exchanger rusted. Igniter showing signs of ware. Cleaned burners. Ventor motor showing signs of bearing ware. Cycled system. Average life of this system is 14 years old. Recommend yearly service on both ac and furnace systems to ensure longer life. Found aprilaire system fan is seizing on operation. Recommend new aprilaire system. Quoted pkg clean and tune, electrostatic filter, and uv light. Furnace cleaning complete.
Performed a clean and tune up on the furnace. Found the flame sensor was dirty and burnt up. Weâ€™ll call back with a price to replace the flame sensor. This is what was causing the furnace to not heat. The furnace is operating at this time. Call to schedule rick to come out and give geo thermal estimate. Call to give price for flame sensor replacement Weâ€™ll come back in the spring to clean ac.
We will remove the old furnace and relocate the new furnace. We will remove and replace all of the duct work in the attic. We will remove and replace the air conditioner.furnace installation complete,ac installation complete,390 lbs of nitrogen on system, needs vacuum pulled and start up done on ac,if registers need to be replaced, we have to do a separate quote at a later date
I completed a level 2 preferred customer cleaning on the Tempstar furnace. I cleaned the igniter and flame sensor. Inspected the heat exchanger. Took readings on the exhaust. Everything is looking good. The A/C hasnâ€™t been cleaned yet, I recommend have it cleaned.
Full furnace clean and tune. Checked system. Cleaned burners, flame sensor, and spark igniter. Ok. Checked heat exchanger, ok. Cleaned cabinet. Checked sequence of operation, ok. System operating normal at this time. Quoted electrostatic filter, top load. Office to schedule ac clean and tune this spring.
Was here for a furnace cleaning. Performed preferred customer furnace clean. The heat exchanger looks old and rusted. No co in the airstream. Inducer motor bearings are worn. Completed furnace cleaning form. Furnace is running at this time.
Exhaust Motor Replacement with a Preferred Customer Clean & Tune I replaced the exhaust motor on the boiler. Also performed a boiler clean and tune. The boiler is operating properly at this time. Dean temporarily fixed the exhaust pipe but found itâ€™s not up to code and should be replaced with pvc. Dean will work on getting a price for that.