The technicians came in took care of everything very fission Attley left the place clean very happy with the service
The AC installation/Electrical crew from Haaks installed a new mini-split air conditioning system in my home. The guys were great and did a class act installation job for me, very happy. Early to tell how the AC will cool, but the heat works great. The team was fantastic to work with and answered all and any question that I had on the system. I could not be happier for the nice installation job performed. Thank you Haaks Team, I look forward to a nice cool home this summer. Dave & Lynn McCoy
Trouble with my furnace which Gary fixed in a matter of minutes and then cleaned it as well.
Always fast and efficient follow up with my geothermal issues.
I'm sure the work that was done was performed very well. However, he did not communicate well from the time he stepped in the house until when the work was complete. Also, I had to leave work early since he was running 45 minutes ahead of schedule.
Placed order for new heating furnace and air conditioning 1/28 and Craig and Connor completed installation of both 1/29.
Woke up to no heat. Black Haak responded and arrived within 45 minutes. Evan quickly determined the problem. Luckily we were under warranty and the necessary parts were replaced. Preventive parts also were replaced under warranty. Great job!
Installed Daikin Gas Furnace - M#DM96SE0603BN S#1912646906 Installed Honeywell Wi-Fi Thermostat - M#TH4110U2005 S#2006JC904542 Completed Gas Furnace replacement. Disconnected and removed old furnace and then set new one in its place. Reconnected the gas, electric, PVC vent pipes, and duct-work to new furnace. Installed a new WiFi Thermostat and connected it to the Furnace. Run tested the furnace. hank you for choosing Black-Haak Heating. Please take a moment to fill out our online survey.
Installed new A/C and took the old one out. Put a new pad down and flushed the line set. Hooked it up and pressure tested the line to 400 psi. Put it in a vacuum down to 355 and released the charge. Will need to come back and do a start up.
Mini split air conditioner install
Air conditioner replacement
Furnace and air conditioner replacement
Install propane furnace
On arrival all the zones were up to temp. He was 37 at an incoming temp of 32. Temp rise was 20.5 with et of 70. I performed a leak search. The leak search was inconclusive. I took a water sample. Replace tstat in the main area and programmed it. The old one was sending a emergency heat call when it wasnâ€™t and it would register on the tstat. Changed some setting on the ewc board to make the stagging operate off the tstats and not the zone board timer. Changed the alpha pump to ramp speed 3. Geo btu output is with in operating limits and no refigernt leaks found. Left the manual for the thermostat on the table. Thanks Brad
Install desuperheater preheat tank and temp controller for the buffer tank. Purge the air out after installing the tank. Test temp controller and set for 95 degrees and to turn on at 90. Test all components and evething is working properly. Thanks Brad
Replaced both capacitors in the geos and cycled them. Geos started up and no other problems found. Both geos are operating properly at this time. Thanks Brad
Water was dripping from inside the geo unit, and leaking out. Found a few Spots that where not insulated well and put some more over the top to make them air tight. Cleaned up the water inside of the unit. Showed the customer where it was coming from and what I was going to do. We also went through all the filters and replaced them (hepa, electronic, and water filter). Did a quick proformence test, 6.5 gpm and a 9 delta t 29,250btus. The geo system is operating properly at this time. Thanks Brad
Installed stair mats for him and made sure all the holes outside were caulked.
Findings Inducer motor tested at 4.9 amp max rating is 3.7amp System tripped on hi limit during tune up. Condensation at leak collector box Rusting in inducer box area X air Is 102.9 Flame sensor has rust on wiring attachment Inducer motor Collector box Flame sensor Hi limit switch All part recommend for replacement Removed, cleaned and installed gas burners Removed, cleaned and installed flame sensor Inspected heat exchanger Tested igniter Checked condensate trap Checked blower motor Checked and tested ventor motor Checked filter Adjusted gas outlet pressure to OEM spec Tested indoor coil. Dan Fox second opinion Now scheduling spring AC tune ups