Dan was awesome and very friendly. He did a very thorough job and educated us on all our options. We would recommend him to anyone.
Follow-up to installation in and out. Testing completed and settings verified, efficiently and promptly.
The BH team did a great job. They were in and out quickly. Installed the new furnace during the coldest temps. Left the furnace room very clean.
It’s a nice feeling when your technician is the same guy for the last 3 years ! Brad was great and thanks for the tips - Black Haak you have been helping me for over 15 years now. I am glad you hire and retain good employees it’s a big reason for our continued patronage .
Hunter was very knowledgeable, polite and engaging. Enjoyed having him service our furnace and would like him to do all our service!
Hunter was friendly and professional.
Our service tech Brad was really great, he was very respectful, explained everything very well, and he even arrived earlier than quoted - if I were reviewing him and him alone, he’d get a 10/10...but we needed a part for the heater - and there was over a 300% markup on it. Exact same part available all over online for $200 or less, but we were charged over $600...I get that profit isn’t a dirty word, but that’s honestly highway robbery - and taking advantage of a family when it’s -25 degrees outside.
Performed furnace clean and tune; inspected the exhaust and intake PVC ensuring all connections were secured, cycled the system on and checked gas pressures, as well as performed a combustion test verifying no CO in the airstream. I do recommend replacing the hepa and pre filter. This system is currently operating normal at this time. Job complete
Furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked and cleaned burners and flame sensor. Checked and adjusted gas pressures to maximize efficiency. Checked for levels of CO and XS air in exhaust. Normal levels found. No CO found in airstream. System operating normal at this time. Found damage to two wire to ac. Looks like it may have been chewed on by a pet. I taped up wires. Looks like the integrity of the wires are intact at this time. System operating normal at this time. Job complete. Quotes given for whole home humidifier and dehumidifier. 600
No heat. The furnace wouldnâ€™t stay lit. Cycled the furnace. The burner flame would come on for a couple seconds and go out, I removed the flame sensor. Found it was dirty. I cleaned the flame sensor, re installed it and cycled the furnace. Itâ€™s operating properly. I recommend having annual maintenance done to furnace and air conditioner. The office will call to schedule the cleaning.
Performed furnace start up; inspected the exhaust and intake PVC ensuring all connections were secured, sniffed the gas line for possible leaks, cycled the system on and checked gas pressures and did make an adjustment to 2nd stage, as well as performed a combustion test verifying no CO in the airstream I did get the temp rise up to 56. This system is currently operating normal at this time. Due to the filter condition I am including a quote for an electronic air cleaner to help bring the down the levels of dust in the home as well as to reduce strain on the furnace. Job complete
Was here to finish mini split set unit and pad need to return in summer to level out the units also need to return to pull unit in vacuum it has 250lbs of nitrogen on it as of now. I cut in coil ran line set for main ac and put unit in the garage need to return to finish outside stuff also will need a wip for electrical connection. We were here to do the start up on both the furnace and mini split unit. For the furnace, no gas leaks were detected. Gas and exhaust levels are normal. No CO detected in the air. Heat rise was 44 degrees. High limit passed the safety check. Unit is heating properly. For the mini split, we were at 250 psi and by the time we finished, we had a 30 degree temp rise. Unit is operating normally at this time.
3-19-19. Removed oil tank and fill lines. Patched holes in garage and sealed line running through concrete in basement. Thank you for choosing Black-Haak heating.
Installed new Goodman furnace. New gas piping, venting, electrical, drain. All up and running.
3-19-19. Removed old furnace. Installed and hung new daikin furnace. Installed metal to connect furnace to duct. Reconnected electrical and thermostat wiring to furnace. Connected pvc to exhaust and intake on furnace. Ran new drain hose from furnace and coil to floor drain. Installed and setup t6 WiFi stat on main floor. Started and tested furnace, running and draining properly. Thank you for choosing Black-Haak heating for your heating needs.
Performed furnace clean and tune; inspected the exhaust and intake PVC ensuring all connections were secured, removed and cleaned the burners along with the flame sensor, cycled the system on and checked gas pressures and did make adjustments on both stages, also performed a combustion test verifying no CO in the airstream. I did inspect the humidifier and found that the water shut off solenoid valve has failed office to quote repair. I also took a peek at the AC evaporator coil and did find some indicators of a possible leak I recommend a clean in tune this spring so we can ensure operations this summer. This system is currently operating normal at this time. Job complete
Installed three dampers on the east side of the plenum to divert the air to the west side. I also up sized the first foot of duct on the south side. Let it run and adjust dampers after a week of run time, this will give the house a chance to adjust and you a chance to see what kind of affect it is having. Thank you for choosing Black Haak Heating
Furnace was constantly running and the air conditioner was running when I arrived. I checked the thermostat wiring, I found the wiring in the thermostat was all bare wire. I fixed the thermostat wiring. The air conditioner would still run. I checked the air conditioner and found it had a mouse nest in it. I removed the mouse nest and repaired the damaged wiring. The furnace and air conditioner are working properly now. Office will call to schedule the air conditioner clean and tune.
No heat upon arrival. Found the igniter cracked. Replaced the igniter and got the sytem running. I did perform a combustion test and did receive over 300ppm of Carbon monoxide going out of the exhaust. Because of the failed heat exchanger this system is currently not safe to operate at this time. Replacement of the system is recommend second opinion scheduled with Jamie. Job complete
Performed preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Cleaned the drain line and drain trap. Cycled the furnace. Checked the gas pressure. Performed furnace combustion test. The furnace is running normally at this time.
Replaced blower motor and performed furnace clean and tune. Removed and cleaned the flame sensor, cycled the sytem on and checked gas pressures, as well as performed a combustion test verifying no CO in the airstream. Ohmed out the igniter which did test weak. As well as noticed the inducer motor was grinding this will eventually lock up like the blower motor. Due to the age, condition, and cost to repair I highly recommend replacement of the furnace. Mr Martinez would like quotes on a new inducer motor/igniter as well as a quote for a new furnace. Second opinion scheduled with Dan F. Job complete
Installed new gas furnace with WiFi thermostat. New pvc, gas piping, electrical, and low voltage, new April air 600.