Dan is courteous and friendly. He did a great job and fully explained the work that was completed.
Service was on time, good service
The service call was on time and well done. Julian was efficient and personable. Should have advised me about servicing the AC at extra cost prior to doing it. It was OK because it should be done but a heads up would be nice.
Dan seemed very thorough not only cleaning and testing everything but explaining things I had asked him about the system.
Great service work and on time service
Our installation of a replacement furnace was done very well. Black-Haak knows what they are doing!
Although it started a little shaky, reason for only 4 stars, it ended up being pretty good. Guys were professional and truly experienced. They did excellent work. Would recommend to anyone!!
Thought you could have moved the unit closer to our home. We asked if we should remove the plant, and you said you had a shovel to move it out of the way. When it was all done, the plant did not get moved, and the unit seems to be out away from the building a little too far. Also, you sent someone out the day prior to measure. He was supposed to get here at 8:30, and didn't arrive until 8:50. This made getting to work on time difficult.
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter Inspected and tested inducer motor and blower motor Checked your condensate drain trap Furnace working well at this time Fixed leak on drain line and changed humidifier pad
System working when I arrived. Filter good, blower motor okay Most likely hi-limit switch Once tripped it will shut off gas valve and run fan until it cools down No charge
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter Inspected and tested inducer motor and blower motor Checked your condensate drain trap Furnace working at this time Pulled blower and inspected secondary heat exchanger There is a water leak from the back of the inducer assembly- recommendation is a new gasket Primary heat exchanger in burner 1 and 2 show excessive wear and will need yearly inspections System is 20 years old, average life expectancy is 14. Office to set up new furnace appt..
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 64Â°. Unit is heating properly. I replaced the drain for the Humidifier.
Start up completed
Replaced flame sensor. Ran and tested unit. All systems operating properly at this time. Have a wonderful fall, Brennan
Performed a preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace. Performed a furnace combustion test. No issues with the furnace at this time. Replaced both the hepa filters. Cleaned the air to air filters. Checked the humidifier pad. The humidifier pad looks ok.
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger is rusting and chipping but no cracks located at this time. Combustion readings were normal. No CO detected in the air. Drain is clear. Heat rise was 47Â°. The flame sensor is warped and needs to be replaced. Part is covered under the parts warranty. We will return with the flame sensor later. Unit is heating properly at this time.
Performed furnace clean and tune. I replaced the oil filter and oil nozzle. Cycled the furnace. The furnace is operating properly at this time. We will return in the spring to clean the air conditioner.
Ac clean and tune. No cool. Cycled system. Furnace fan kicked on, but not condenser fan or compressor. Opened electrical compartment. Tested capacitor. Found capacitor has failed and is below tolerance. Replaced with new 35/5 capacitor. Cycled system. Condenser fan and compressor fired. Used coil cleaner on condenser coil. Hooked up gauges and checked pressures and temps. Found indoor coil at 38 degrees, subcooling was 8, indoor temp split was only 12. Checked indoor coil with refrigerant sniffer. Found indications of a leak forming on indoor coil. Tested compressor and fan motor. Compressor tested ok. Fan motor tested low, but still in the normal range. Average life expectancy for this unit is 14 years. This system exceeds this expectancy, and unit is very worn. Future failure is expected. Second opinion is recommended. Job complete.
Performed preferred customer air conditioning cleaning. Replaced the drain line. Cleaned the condenser coil. Checked the electrical. The electrical is ok. Cycled the air conditioner and checked the refrigerant levels. No issues with the air conditioner at this time.
Pull new thermostat wire and wire for ac condenser. Insatll new T6 thermostat program. Reconnect all wires and test ac and furnace. All systems are operating properly this time. Thanks Brad
Performed package clean and tune; inspected the exhaust and intake PVC ensuring all connections were secured, removed and cleaned the burners along with the flame sensor, cycled the system and checked gas pressures, performed a combustion test verifying no CO in the airstream I did receive higher than normal amounts of CO and excess air in the exhaust future failure of the heat exchanger is expected. Also inducer motor failed at 60%. I then cycled the UV light on Bob had mentioned he just replaced the uv light bulbs this system was installed 17 years ago office to quote ballast replacement/new Uv light. I then cleaned the AC system, inspected condenser electrical compartment and tested components the capacitor tested ok but is showing wear as for the fan motor is rated for 1.1 amps and I pulled .6 these components are expected to fail. These systems are currently operating but there is no guarantee for how long. I highly recommend looking into getting them replaced in the future possib
Trnasfer switch could not be mounted. In the house panel was in a finished room in the basement and access to the unfinished basement was not possible. Installed generator interlock kit and inlet instead of transfer switch. Homeowner said he will try it and if it does not work out for him we will need to order an outdoor rated transfer switch for him.
Preformed cleaning and system evaluation on find out why the one u it isnâ€™t cooling enough. The fan for the master bedroom is plugged with lint and dust. We will need to research the best way to clean the indoor unit and return to do that. I couldnâ€™t get a vacuum in there and there was no way to get one in there. The rest of they system looks good no other problems of issue with it. Thanks Brad