Fast; on time; professional. I would recommend to others.
Both Bill and Mark our two installers were great. They were prompt, skilled, efficient, and personable. High marks. We’ll certainly deal with Black-Haack again.We’ve had other personnel from Black-Haack and each has been very good.
Great, friendly, prompt service
Service person was very knowledgeable, shared a lot of information regards heating /AC unit maintenance, Was very polite. courteous. Very thorough. ID'ed current condition and future upkeep of Unit. learned much more of our system then what we had known. Very impressed with Black Hawk.
Very pleased with the service would recommend to anyone
Tech was respectful of house, seemed knowledgeable, professional, and clear.
Silicones and taped the air leaks on the ac system and everthing is operating properly at this time. Thanks Brad
Ac clean and tune. Checked indoor coil with refrigerant sniffer. Found some indications of possible leaks on that coil. Cycled system. Found rodent nest in condenser. Wires have been repaired in past visit. Found capacitor worn. Tested compressor and fan motor, both tested low with megohmeter. Used coil cleaner on condenser coil. Condenser coil damaged and full of mold. Hooked up gauges and checked pressures and temps. Indoor coil temp was 39. Subcooling was 9. Indoor split was 16. Due to age, condition, and cost to repair, second opinion is recommended. Future failure is expected. Office to follow up with payment and to see about scheduling a free option consultation, to prevent expected major expense due to critical failure. Job complete.
Performed 1st year cleaning. Did not find any issue with the furnace at this time.
Ac clean and tune. Cycled system, cleared drain lines. Checked filter. Recommend changer pad before cooling season. Checked and cleaned electrical compartment. Checked capacitor and compressor, itâ€™s ok. Checked contactor, ok. Used coil cleaner on condenser. Cycled system. Checked pressures and temps, both ok. Checked temp split, found 19. System operating normal at this time. Job complete.
Cut in humidifier unit. Installed unit. Ran water line to water heater. Installed saddle valve. Hooked up water line. Cut in bypass and installed 3 90 degree elbows and 4â€™ of 6â€ round pipe. Attached. Cut in control. Wired control to main board and unit. Installed transformer and wired power to main control. Ran drain line from unit and cycled system. Unit operating normal at this time. Job complete.
Furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked and adjusted gas pressures to maximize efficiency. Checked and cleaned burners and flame sensor. Both ok. Checked electrical connections, ok. Checked operating system. Checked for levels of CO and XS air in exhaust, both within normal range. No CO found in airstream. System operating normal at this time. Job complete.
Performed preferred customer furnace start up. Checked over the furnace installation. Cycled the furnace. Set the gas pressure. Took a temperature rise and set the fan speed. Performed furnace combustion test. The furnace is running normally at this time.
Completed Gas Furnace replacement. Disconnected and removed old furnace and then set new one on blocks in its place. Reconnected the gas, electric, PVC vent pipes, and duct-work to new furnace. Run tested the furnace, but will still need a technician start up. The Office will follow up to schedule a technician to return to do the Furnace efficiency startup, which is required for warranty purposes. Thank you for choosing Black-Haak Heating. Please take a moment to fill out our online survey.
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Gas and exhaust levels are normal. No CO detected in the air. Drain is clear. Heat rise was 42 degrees. Unit is heating properly at this time. There is a moisture stain on top of the unit. I didnâ€™t find any signs of water damage or rust in the furnace or any leaks in the surrounding area. Pictures were uploaded. Looks like water came from the fresh air pvc so I tightened the pipe a little more.
Performed preferred customer 1st year furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped done the inside of the furnace. Cleaned the drain line. Cycled the furnace. Checked the motors for proper operation. Performed furnace combustion test. The furnace is running normally at this time.
Furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked and cleaned burners and flame sensor. Checked and adjusted gas pressures to maximize efficiency. Checked levels of CO and XS air in exhaust, ok. No CO in airstream. System operating normal at this time. Office to schedule ac clean and tune in spring. Paid. Installed electronic air cleaner.
Performed preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the heat exchanger. Wiped down the inside cabinet. Cycled the furnace. Checked the furnace motors. Performed furnace combustion test. The furnace is running normally at this time. The humidifier pad looks like it should be replaced. Called the customer. The customer is not interested in changing it at this time.
Fixed return duct was poping in and out put s slip on it.
Replaced gas valve under warranty. I cycled the system on and adjusted gas pressure to 3.5inH20. This system is currently operating normal at this time. Job complete
Performed level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Gas and exhaust levels are normal. No CO detected in the air. Drain is clear. Heat rise was 59 degrees. Unit is operating normally at this time.