We had the furnace put in our home w/ air conditioner as an option after some remodeling is to be done. This entails moving the present A/C unit and replacing this unit. The contractor said they would be handleling this phase of the remodel also. We wish to allow the contractor do the A/C work that is in the bid. Thank you for your option on the A/C unit but we will go with what is stated. We still will use your service in the future.
Black-Haak always provides excellent and friendly service as well as great communication; they call before arrival and follow up if a repair was necessary to ensure satisfaction.
Performed level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger is showing minor signs of wear. Gas and exhaust levels are normal. No CO detected in the air. Drain is clear. Heat rise was 44*. Investigated the humidifier. It appears to be okay. Display shows 39%. Might not be kicking on due to the warmer and damp weather. Unit is operating normally at this time. Thank you for choosing Black-Haak! Please take the time to complete our online
Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. The furnace is running normally at this time. Customer would like a call in the spring to schedule a possible air conditioning cleaning.
Checked power on breakers in breaker box. Checked power in office. Checked power for garage freezers. Replaced owner supplied fuse in fuse box in workshop. All power is back on.
I was here to replace the gas valve in the furnace. I set up the new gas valve to lp. I replaced the gas valve and wired it to the furnace. Cycled the furnace and set the gas pressures. I checked the temperature rise and itâ€™s at 55 which is good. Checked for gas leaks, found a leak and fixed the leak. The furnace is operating properly at this time. No charge, part is under warranty.
Was here for a boiler cleaning. Performed preferred customer boiler cleaning. Cycled the boiler the boiler would not fire up. Called Dan Fox. Dan sent out Jeremiah. Figured out that the flame sensor was touching to ground causing the boiler to see a flame. Readjusted the flame sensor. The boiler fired up. The boiler is running normally at this time. The customer is getting a free air conditioning cleaning. Office to call in the spring to schedule the air conditioning cleaning.
Performed start up on new Tempstar furnace. No gas leaks detected. Combustion analysis was normal. No CO detected in the air. Drain is working. Electrical and venting is properly installed. High limit passed safety test. Heat rise was 58 degrees. Unit is operating normally at this time.
I replaced the blower motor and the blower control board. I cycled the furnace. Itâ€™s operating properly at this time.
Performed furnace start up. No gas leaks detected. Combustion analysis test was normal. No CO detected in the airstream. Unit is operating normal at this time. Sold and installed a polarized electrostatic filter. I showed the customer how to safely and properly change the filters.
Installed Daikin Gas Furnace M#DM96VC080 S#1708268662 Removed the old furnace and installed a new gas furnace. Tied into the existing gas line and venting. Ran a new drain line. Installed a new thermostat. Customer paid $5,208.00 at this time for just furnace. When we return to do AC they will pay balance of $4,391.00. Will still need a tech start up. Thank you for choosing Black-Haak. Please take a moment to fill out our online survey.
Performed level 2 AC clean and tune. No leaks detected at indoor coil. Electrical components tested good. Condenser coil is clean. Refrigerant charge was good. Unit is operating normal at this time.
Was here to replace the roof top unit filters. Replaced the roof top unit filters.
Performed level 2 AC clean and tune. No leaks detected at indoor coil. Electrical components tested good. Condenser coil is cleaned out. Refrigerant charge was normal. Temp split was 17 degrees with a 12 degree subcool.
Performed level 2 package cleaning. Furnace. Cleaned flame sensor and burners. Wiped away any dust in blower and burner compartments. Inspected heat exchanger. Cleared drain hose. Combustion test was normal. No CO in airstream. AC. No leaks detected at indoor coil. Electrical components tested in the caution area. Refrigerant charge was normal. Temp split was 17 degrees. HVAC system is operating normal at this time.
I replaced the pressure/temperature gauge that was leaking water. Bleed the air out, system is operating as normal. System is under a year old, covered under company warranty.
I completed a level 2 preferred customer cleaning on the Tempstar furnace. The heat exchanger has mild rust. The igniter and flame sensor are both good. The gas pressures are good. The furnace is running safely. I changed the Aprilaire 213 filter media. I used my refrigerant leak detector on the indoor coil and found a couple leaks, the unit is older and it could be beneficial to hear some options on A/C equipment.