The technician was prompt, efficient, and explained everything he did.
Professional pleasant knowledgeable and efficient
I think Browns does a super job, techs are professional, office follows up and they do a very good job. My home owners insurance sends our other hvac guys, but Browns is clearly a better quality operation
Very good service.
He came before schedule time which I really appreciated. Explained everything that had to be done. Very satisfied with their service set up maintenance plan.
We've been using Brown Heating & Cooling for 17 years since 2002 and they have always been great. Derek Perkins has especially been good over the last few years. He is always very personable and professional.
2003 carrier AC
Maintenance on a 2009 Nordyne air-conditioning system
Arrived at customer’s house to perform cooling maintenance. Cleaned outdoor unit, cleaned condensate pump, checked refrigerant charge, proper operation in cooling mode, checked capacitors, took amp draws on motors and compressor. Took delta t, new filters were provided. System was operating at time of departure
Repaired refrigerant leak.
Arrived at customers home to install new heating and cooling system checked operations had to make a return trip to complete all operations were in good working order at time of departure thank you for the opportunity to earn your business.
Arrived at customer’s house to perform cooling maintenance. Checked refrigerant pressures, proper operations in cooling mode, cleaned outdoor coil, checked amp draws on all motors, took delta t. Changed filter. System was operating at time of departure
Maintenance on a 2006 Frigidaire air conditioning system
Performed cooling maintenance at customer’s house. Cleaned condenser coil, checked amp draws, checked capacitors, checked refrigerant charge, proper operation in cooling mode. System was operating ok
Diagnosing a refrigerant leak
Arrived at customer’s house to perform cooling maintenance. Cleaned outdoor coil, checked compressor and fan motor amp draws, checked capacitors, checked for proper operation in cooling mode. Took delta t. System was operating at time of departure.
Did cooling maintenance on system at customer’s house. Checked refrigerant charge, cleaned condenser coil, checked delta t, changed filters, checked proper operation of system in cooling mode. Checked amp draw on motors.Temperature was set back to desired temperature. System was operating at time of departure.
Maintenance on a 2013 Bryant air conditioning system