Excellent service. Very informative and gave several options for service. The technicians update you as to their arrival. They take their time while servicing the units and explain all options for maintenance and repair. Highly recommend Brown’s Heating and Cooling.
Jason just did our bi-yearly maintenance and was extremely competent, friendly, and answered all of our questions thoroughly. I will continue to spread the word about Brown’s maintenance plan because it is affordable and has really paid off for us.
Explained everything throughly. Made sure we understood. Very pleasant to work with.
Oliver is always professional. He goes to work quickly and explains what he has done or if there were any issues.
Had my annual Heating Maintenance, great service and on time! Technician was very professional!
Brown, Heating & Cooling Technician, Oliver Kessels, arrived at my residence to perform a regular check up of my system per my maintenance agreement with them. As luck would have it, my unit had also stopped working. Mr. Kessels went right to work and found that I had a breaker problem that prevented my heating unit from working and made a few recommendations to me. Mr. Kessels is a very hard, diligent and courteous worker, as are all the other BH&C techs that have been to my home in the past years, and I appreciate their work. It is a good feeling to have a company who consistently cares about their products and their customers. And thanks to Mr. "Oliver" and the Good Lord, I had heat again within 2 hours! I am still amazed and so grateful!!!
Maintenance on gas furnace
Arrived at customers home to perform heating maintenance checked all heating operations all checked out ok at the time of inspection
Replaced vent pipe for a furnace and water heater! Thank you!
Service call. Unit not heating
Performed heating maintenance at customer’s house, checked filter, checked delta t, tested system for proper operation in heating mode, checked emergency heat, washed outdoor coil, system was presented to customer at departure
Performed heating maintenance at customer’s house, changed filter, checked system for proper operation in heating mode, checked delta t, presented system to customer at departure.
Arrived to perform heating maintenance. Checked motors capacitors amp draws and connections. Clean flame sensor and pressure to port and blower and coil were clean. Checked gas pressure delta T changed batteries and filter. System functions properly at this time.
Performed heating maintenance at customer’s house, changed filter, checked for proper operation in heating mode, put settings back on thermostat as requested, took delta t, system functioning properly at departure
Arrived at customers home to perform heating maintenance maintenance informed customer combustion blower motor has issues and will be needing replaced customer would like to replace at next visit
Arrived at customers home to perform heating maintenance checked all heating operations all checked out ok at time of departure