Chrome has been professional, timely, fair and wonderful to work with throughout our winter storm repairs and tankless water heater replacement. I highly recommend them for any plumbing or HVAC needs.
John was very personable and did a fantastic job
With the Texas storm, I received a fast response and had an appointment immediately. The service tech was very knowledgeable and honest with his service!
Customer will need a two system tune up. Discovered copper drain line over patio leaking and needing a 10 foot section of drain pipe replaced. Also discovered dryer exhaust blowing out into the attic with no exit to the outdoors. Will send customer estimate to make proper repairs.
Did estimates for sealing ductwork and applying Pure Air replacement
Customer would like to replace complete system..... Thursday 04/15/2021 would like to pay in full.
Filters were clean, checked call for cooling, voltage on lines and board, unit was clean, checkeds charge and pressures, checked temp splits
Checked temp splits, voltage on board, transformer, and lines, checked proper temp and levels on condenser, noted filters are dirty and customer would like to replace themselves, everything else very clean and we'll insulated
Checked temp splits, indoor furnace voltages to unit, filter were clean, unit and coils made sure were clean, checked outdoor coils and superheat and charge, operating functionally
Installed Nest thermostat, checked temp split, checked charge by superheat and subcooling, replaced client provided air filter, amps on compressor, ensured system was clean
Check wiring connections made sure all was correct ... no lose connection's... blowed drain line.. we had no extra thermostats on truck told customer if thermostat malfunction again to take a picture of it.... thermostat may need to be replaced if problem persist.
Unit was low on refrigerant but been having issues since we installed it system needs to be leak checked.
Furnace fan motor needs to be replaced. Carrier
Filters clean, unit working properly, fixed insulation coming off of inside furnace blocking blower motor, checked superheat and temp splits. Have dust problem, recommend estimates for resealing ductwork, duct cleaning, and possible air scrubber.
Rats ate thermostat wire ... wire needs to be repaired but they would like to address pest problems first and also become a Chrome member.
Replaced client provided filter. Checked temp split and at optimal temps. Checked cooling functionality at thermostat and circuitry in air handler. Unit clean and operational. Checked pressures and charge via superheat, at 12 degree at good temp.
Unit cleaned.... pressure/temperature check... outside temperature too low to know if unit needs refrigerant only a 2degree super heat ... refrigerant would need to be checked when there is a heat load.
Dampers were adjusted customer was satisfied with pressure coming out of Supply registers.