Good communication. On time. I signed up for yearly maintenance. Jeremy our tech was professional and informative
Never will used this company again
Answered all my questions
these guys gave an estimate but doesnt tell what part numbrr are they replacing.. they told would gove teo quotes - one without replacing and one with replacing.. but got only one.. talked to manager.. she was adamnant they wouldnt give info about the part they going to replace with.
I was cancelled on multiple times last minute, misled on pricing, and then overcharged for my service with the owner of the company lying directly to me. The actual plumber that performed the work was nice and did a good job.
He is very knowledgeable and does a great job communicating. Great guy.
Upon arrival found system not heating. Found gas line off and 1st panel taken off. Turned system on and found that my pressure switch wasnâ€™t closing. Checked pressure switch and it was good, checked port for pressure switch on the draft motor and found it clogged. Cleared hole and reconnected switch. Furnace is now operating properly. I did notice the blower starting up slow and checked capacitor, reading was 5.5 out of 7.5. Recommended replacing the capacitor, homeowner approved repair, replaced capacitor and checked amp draws on motor. 4.3 out of 8.2. System is now working properly at this time.
Checked amp draws on inducer fan motor and blower motor, cleaned flame sensor checked air filter, checked safety devices, checked heat exchanger it was good, check igniter
Checked amp drawâ€˜s on indoor blower, checked Heat strip amp draws checked freon pressures on heat pump, checked condenser fan amp draws and compressor amp drawâ€˜s, when out at the condenser and saw some possible oil line on the coils, everything is operating at this time
Checked amp draws on inducer fan motor and blower motor, cleaned flame sensor checked air filter, checked safety devices, checked heat exchanger it was good, check igniter. Customer mentioned secondary drain was dripping upon looking at main drain line found that main drain was clogged up and recommended blowing out, and recommended a float switch
Checked amp draws on inducer fan motor and blower motor, cleaned flame sensor checked air filter, checked safety devices, checked heat exchanger it was good, check igniter, everything is operating correctly at this time
Checked amp draws blower motor, checked air filter, checked condenser fan amp drawls checked compressor amp drawâ€˜s, the homeowner informed me that the heat pump was not hooked up, at the condenser unit y1 was jumped out to the O terminal, homeowner was unsure about hooking up the heat pump function
Assisted hunter with maintenance, main drain line was clogged up, recommended blowing out drain line. Landlord approved blowing out drain line. Cut line and blew out line with nitrogen. Poured water down drain to ensure clog was cleared. System is now draining properly.
Assisted hunter with maintenance
Disconnected incorrect zone board and installed correct zone board. Connected 2nd stage heat and cooling. Set zone board to where when both zones call it puts system into second stage. Tested system and system is now working properly.
Gave estimates to replace 3.5ton heat pump system, gave pricing for a 14seer 16seer and 20seer. Homeowner was not home but approved us being there to give replacement options. Homeowner hasnâ€™t shown up after waiting 20min after we were done. Left options sheet on counter and left message to cal if anything questions.
Performed a one system maintenance checking heating. Checked inside units electrical and mechanical components, checked gas pressures, heat exchanger, blower and draft motor amps, filter, cleaned flame sensor, furnace is heating properly at this time. Recommended adding a uv alight/air scrubber to the system. Homeowner signed up for maintenance annually
Assisted hunter with maintenance, recommended adding air scrubbers and surge protectors to units.
Found upstairs Tstat blank, checked inside unit and found power off to unit. Turned power backbb by on and tstat came on and system is operating properly at this time.
Installed 2 Navian exterior tankless water heaters. NPN199E
Performed a 5 system maintenance checking heating, changed all filters, checked electrical and mechanical components, checked heat exchangers, draft and blower amps, cleaned flame sensors, checked all safeties and pressure switches, all systems are heating properly at this time.